Charlie
type: site
has tag: site
area: 50000
dis: Charlie
geo addr: 123 Some Rd, Troy, MI 48007
geo city: Troy
geo country: US
geo postal code: 48007
geo state: MI
geo street: 123 Some Rd
primary function: Office
tz: Detroit
weather station ref: Troy, MI
year built: 1995

Charlie AHU 1
type: ahu
has tag: ahu
has tag: equip
dis: Charlie AHU 1
site ref: Charlie
custom: {equipGroup:AHUs}
  equip group: AHUs

Charlie AHU 1 CO2
type: cur-point
type: his-point
has tag: air
has tag: co2
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: zone
dis: Charlie AHU 1 CO2
equip ref: Charlie AHU 1
kind: Number
site ref: Charlie
tz: New_York
unit: ppm

Charlie AHU 1 CO2 Setpoint
type: cur-point
type: his-point
has tag: air
has tag: co2
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: zone
dis: Charlie AHU 1 CO2 Setpoint
equip ref: Charlie AHU 1
kind: Number
site ref: Charlie
tz: New_York
unit: ppm

Charlie AHU 1 Chilled Water Valve Status
type: cur-point
type: his-point
has tag: chilled
has tag: cmd
has tag: cur
has tag: his
has tag: point
has tag: valve
has tag: water
dis: Charlie AHU 1 Chilled Water Valve Status
equip ref: Charlie AHU 1
kind: Number
site ref: Charlie
tz: New_York
unit: %

Charlie AHU 1 Discharge Air Pressure
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: pressure
has tag: sensor
dis: Charlie AHU 1 Discharge Air Pressure
equip ref: Charlie AHU 1
kind: Number
site ref: Charlie
tz: New_York
unit: inH₂O
custom: {precision:2}
  precision: 2

Charlie AHU 1 Discharge Air Pressure Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: pressure
has tag: sp
dis: Charlie AHU 1 Discharge Air Pressure Setpoint
equip ref: Charlie AHU 1
kind: Number
site ref: Charlie
tz: New_York
unit: inH₂O
custom: {precision:2}
  precision: 2

Charlie AHU 1 Discharge Air Temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Charlie AHU 1 Discharge Air Temp
equip ref: Charlie AHU 1
kind: Number
site ref: Charlie
tz: New_York
unit: °F

Charlie AHU 1 Discharge Air Temp Reset
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sp
has tag: temp
dis: Charlie AHU 1 Discharge Air Temp Reset
equip ref: Charlie AHU 1
kind: Number
site ref: Charlie
tz: New_York
unit: °F
custom: {rest}

Charlie AHU 1 Mixed Air Damper Command
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: his
has tag: mixed
has tag: point
dis: Charlie AHU 1 Mixed Air Damper Command
equip ref: Charlie AHU 1
kind: Number
site ref: Charlie
tz: New_York
custom: {precision:1}
  precision: 1

Charlie AHU 1 Mixed Air Temp Sensor
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: mixed
has tag: point
has tag: sensor
has tag: temp
dis: Charlie AHU 1 Mixed Air Temp Sensor
equip ref: Charlie AHU 1
kind: Number
site ref: Charlie
tz: New_York
unit: °F

Charlie AHU 1 Mixed Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: mixed
has tag: point
has tag: sp
has tag: temp
dis: Charlie AHU 1 Mixed Air Temp Setpoint
equip ref: Charlie AHU 1
kind: Number
site ref: Charlie
tz: New_York
unit: °F

Charlie AHU 1 Occupied Command
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: his
has tag: occupied
has tag: point
dis: Charlie AHU 1 Occupied Command
enum: UnOccupied,Occupied
equip ref: Charlie AHU 1
kind: Bool
site ref: Charlie
tz: New_York

Charlie AHU 1 Outside Air Temp Sensor
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: outside
has tag: point
has tag: sensor
has tag: temp
dis: Charlie AHU 1 Outside Air Temp Sensor
equip ref: Charlie AHU 1
kind: Number
site ref: Charlie
tz: New_York
unit: °F

Charlie AHU 1 Return Air Temp Sensor
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: return
has tag: sensor
has tag: temp
dis: Charlie AHU 1 Return Air Temp Sensor
equip ref: Charlie AHU 1
kind: Number
site ref: Charlie
tz: New_York
unit: °F

Charlie AHU 1 Return Fan Command
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: fan
has tag: his
has tag: point
has tag: return
dis: Charlie AHU 1 Return Fan Command
enum: Off,On
equip ref: Charlie AHU 1
kind: Bool
site ref: Charlie
tz: New_York

Charlie AHU 1 Return Fan Status
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: fan
has tag: his
has tag: point
has tag: return
has tag: run
has tag: sensor
dis: Charlie AHU 1 Return Fan Status
enum: Off,On
equip ref: Charlie AHU 1
kind: Bool
site ref: Charlie
tz: New_York

Charlie AHU 1 Return Fan VFD Signal
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: fan
has tag: his
has tag: point
has tag: return
has tag: speed
dis: Charlie AHU 1 Return Fan VFD Signal
equip ref: Charlie AHU 1
kind: Number
site ref: Charlie
tz: New_York
unit: %

Charlie AHU 1 ReturnFan
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: fan
has tag: his
has tag: point
has tag: return
dis: Charlie AHU 1 ReturnFan
enum: false,true
equip ref: Charlie AHU 1
kind: Bool
site ref: Charlie
tz: New_York

Charlie AHU 1 ReturnFanStatus
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: fan
has tag: his
has tag: point
has tag: return
has tag: run
has tag: sensor
dis: Charlie AHU 1 ReturnFanStatus
enum: false,true
equip ref: Charlie AHU 1
kind: Bool
site ref: Charlie
tz: New_York

Charlie AHU 1 Supply Fan Command
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: discharge
has tag: fan
has tag: his
has tag: point
dis: Charlie AHU 1 Supply Fan Command
enum: Off,On
equip ref: Charlie AHU 1
kind: Bool
site ref: Charlie
tz: New_York

Charlie AHU 1 Supply Fan Status
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: fan
has tag: his
has tag: point
has tag: sensor
dis: Charlie AHU 1 Supply Fan Status
enum: Off,On
equip ref: Charlie AHU 1
kind: Bool
site ref: Charlie
tz: New_York

Charlie AHU 1 Supply Fan VFD Speed
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: discharge
has tag: fan
has tag: his
has tag: point
has tag: speed
dis: Charlie AHU 1 Supply Fan VFD Speed
equip ref: Charlie AHU 1
kind: Number
site ref: Charlie
tz: New_York
unit: %

Charlie AHU 1 SupplyFan
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: discharge
has tag: fan
has tag: his
has tag: point
dis: Charlie AHU 1 SupplyFan
enum: false,true
equip ref: Charlie AHU 1
kind: Bool
site ref: Charlie
tz: New_York

Charlie AHU 1 SupplyfanStatus
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: fan
has tag: his
has tag: point
has tag: run
has tag: sensor
dis: Charlie AHU 1 SupplyfanStatus
enum: false,true
equip ref: Charlie AHU 1
kind: Bool
site ref: Charlie
tz: New_York

Charlie AHU 1 Zone Air Temp Sensor
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Charlie AHU 1 Zone Air Temp Sensor
equip ref: Charlie AHU 1
kind: Number
site ref: Charlie
tz: New_York
unit: °F

Charlie AHU-2
type: ahu
has tag: ahu
has tag: equip
dis: Charlie AHU-2
site ref: Charlie
custom: {equipGroup:AHUs}
  equip group: AHUs

Charlie AHU-2 AHU2-BLD~2dP-SetPoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: pressure
has tag: sp
dis: Charlie AHU-2 AHU2-BLD~2dP-SetPoint
equip ref: Charlie AHU-2
kind: Number
site ref: Charlie
tz: New_York
unit: in/wc
custom: {precision:2}
  precision: 2

Charlie AHU-2 AHU2-BLD~2dPressure
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: pressure
has tag: sensor
dis: Charlie AHU-2 AHU2-BLD~2dPressure
equip ref: Charlie AHU-2
kind: Number
site ref: Charlie
tz: New_York
unit: in/wc
custom: {precision:2}
  precision: 2

Charlie AHU-2 AHU2-CHW~2dValve
type: cur-point
type: his-point
has tag: chilled
has tag: cmd
has tag: cur
has tag: his
has tag: point
has tag: valve
has tag: water
dis: Charlie AHU-2 AHU2-CHW~2dValve
equip ref: Charlie AHU-2
kind: Number
site ref: Charlie
tz: New_York
unit: %

Charlie AHU-2 AHU2-DA~2dP
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: pressure
has tag: sensor
dis: Charlie AHU-2 AHU2-DA~2dP
equip ref: Charlie AHU-2
kind: Number
site ref: Charlie
tz: New_York
unit: in/wc
custom: {precision:2}
  precision: 2

Charlie AHU-2 AHU2-DA~2dP-SetPoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: pressure
has tag: sp
dis: Charlie AHU-2 AHU2-DA~2dP-SetPoint
equip ref: Charlie AHU-2
kind: Number
site ref: Charlie
tz: New_York
unit: in/wc
custom: {precision:2}
  precision: 2

Charlie AHU-2 AHU2-Discharge Air Temp-Reset
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sp
has tag: temp
dis: Charlie AHU-2 AHU2-Discharge Air Temp-Reset
equip ref: Charlie AHU-2
kind: Number
site ref: Charlie
tz: New_York
unit: °F
custom: {reset}

Charlie AHU-2 AHU2-OCC~2dC
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: his
has tag: occupied
has tag: point
dis: Charlie AHU-2 AHU2-OCC~2dC
enum: UnOccupied,Occupied
equip ref: Charlie AHU-2
kind: Bool
site ref: Charlie
tz: New_York

Charlie AHU-2 AHU2-Override
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: occupied
has tag: point
has tag: sensor
dis: Charlie AHU-2 AHU2-Override
enum: Off,On
equip ref: Charlie AHU-2
kind: Bool
site ref: Charlie
tz: New_York

Charlie AHU-2 AHU2-RF~2dS
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: fan
has tag: his
has tag: point
has tag: return
has tag: run
has tag: sensor
dis: Charlie AHU-2 AHU2-RF~2dS
enum: Off,On
equip ref: Charlie AHU-2
kind: Bool
site ref: Charlie
tz: New_York

Charlie AHU-2 AHU2-RF~2dVFD
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: fan
has tag: his
has tag: point
has tag: return
has tag: speed
dis: Charlie AHU-2 AHU2-RF~2dVFD
equip ref: Charlie AHU-2
kind: Number
site ref: Charlie
tz: New_York
unit: %

Charlie AHU-2 AHU2-SF~2dC
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: discharge
has tag: fan
has tag: his
has tag: point
dis: Charlie AHU-2 AHU2-SF~2dC
enum: Off,On
equip ref: Charlie AHU-2
kind: Bool
site ref: Charlie
tz: New_York

Charlie AHU-2 AHU2-SF~2dS
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: fan
has tag: his
has tag: point
has tag: sensor
dis: Charlie AHU-2 AHU2-SF~2dS
enum: Off,On
equip ref: Charlie AHU-2
kind: Bool
site ref: Charlie
tz: New_York

Charlie AHU-2 AHU2-SF~2dVFD
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: discharge
has tag: fan
has tag: his
has tag: point
has tag: speed
dis: Charlie AHU-2 AHU2-SF~2dVFD
equip ref: Charlie AHU-2
kind: Number
site ref: Charlie
tz: New_York
unit: %

Charlie AHU-2 AHU2CO2SetPoint
type: cur-point
type: his-point
has tag: air
has tag: co2
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: zone
dis: Charlie AHU-2 AHU2CO2SetPoint
equip ref: Charlie AHU-2
kind: Number
site ref: Charlie
tz: New_York
unit: ppm

Charlie AHU-2 Discharge Air Temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Charlie AHU-2 Discharge Air Temp
equip ref: Charlie AHU-2
kind: Number
site ref: Charlie
tz: New_York
unit: °F

Charlie AHU-2 Mixed Air Temp Sensor
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: mixed
has tag: point
has tag: sensor
has tag: temp
dis: Charlie AHU-2 Mixed Air Temp Sensor
equip ref: Charlie AHU-2
kind: Number
site ref: Charlie
tz: New_York
unit: °F

Charlie AHU-2 Mixed Air Temp Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: mixed
has tag: point
has tag: sp
has tag: temp
dis: Charlie AHU-2 Mixed Air Temp Setpoint
equip ref: Charlie AHU-2
kind: Number
site ref: Charlie
tz: New_York
unit: °F

Charlie AHU-2 Outside Air Temp Sensor
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: outside
has tag: point
has tag: sensor
has tag: temp
dis: Charlie AHU-2 Outside Air Temp Sensor
equip ref: Charlie AHU-2
kind: Number
site ref: Charlie
tz: New_York
unit: °F

Charlie AHU-2 Return Air Temp Sensor
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: return
has tag: sensor
has tag: temp
dis: Charlie AHU-2 Return Air Temp Sensor
equip ref: Charlie AHU-2
kind: Number
site ref: Charlie
tz: New_York
unit: °F

Charlie AHU-2 ReturnFan
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: fan
has tag: his
has tag: point
has tag: return
dis: Charlie AHU-2 ReturnFan
enum: false,true
equip ref: Charlie AHU-2
kind: Bool
site ref: Charlie
tz: New_York

Charlie AHU-2 ReturnFanStatus
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: fan
has tag: his
has tag: point
has tag: return
has tag: run
has tag: sensor
dis: Charlie AHU-2 ReturnFanStatus
enum: false,true
equip ref: Charlie AHU-2
kind: Bool
site ref: Charlie
tz: New_York

Charlie AHU-2 SupplyFan
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: discharge
has tag: fan
has tag: his
has tag: point
dis: Charlie AHU-2 SupplyFan
enum: false,true
equip ref: Charlie AHU-2
kind: Bool
site ref: Charlie
tz: New_York

Charlie AHU-2 SupplyfanStatus
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: fan
has tag: his
has tag: point
has tag: run
has tag: sensor
dis: Charlie AHU-2 SupplyfanStatus
enum: false,true
equip ref: Charlie AHU-2
kind: Bool
site ref: Charlie
tz: New_York

Charlie AHU-2 Zone Air Temp Sensor
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Charlie AHU-2 Zone Air Temp Sensor
equip ref: Charlie AHU-2
kind: Number
site ref: Charlie
tz: New_York
unit: °F

Charlie B100 BOILERS PUMPS
type: boiler
has tag: boiler
has tag: equip
dis: Charlie B100 BOILERS PUMPS
site ref: Charlie
custom: {equipGroup:Hot Water Systems}
  equip group: Hot Water Systems

Charlie B100 BOILERS PUMPS BLR1~2dC
type: boiler
type: cur-point
type: his-point
has tag: boiler
has tag: cmd
has tag: cur
has tag: enable
has tag: his
has tag: point
dis: Charlie B100 BOILERS PUMPS BLR1~2dC
enum: On,Off
equip ref: Charlie B100 BOILERS PUMPS
kind: Bool
site ref: Charlie
tz: New_York

Charlie B100 BOILERS PUMPS BLR2~2dC-
type: boiler
type: cur-point
type: his-point
has tag: boiler
has tag: cmd
has tag: cur
has tag: enable
has tag: his
has tag: point
dis: Charlie B100 BOILERS PUMPS BLR2~2dC-
enum: On,Off
equip ref: Charlie B100 BOILERS PUMPS
kind: Bool
site ref: Charlie
tz: New_York

Charlie B100 BOILERS PUMPS Boiler-Reset
type: boiler
type: cur-point
type: his-point
has tag: boiler
has tag: cur
has tag: his
has tag: point
has tag: sp
dis: Charlie B100 BOILERS PUMPS Boiler-Reset
equip ref: Charlie B100 BOILERS PUMPS
kind: Number
site ref: Charlie
tz: New_York
unit: °F
custom: {reset}

Charlie B100 BOILERS PUMPS Boiler1
type: boiler
type: cur-point
type: his-point
has tag: boiler
has tag: cmd
has tag: cur
has tag: enable
has tag: his
has tag: point
dis: Charlie B100 BOILERS PUMPS Boiler1
enum: false,true
equip ref: Charlie B100 BOILERS PUMPS
kind: Bool
site ref: Charlie
tz: New_York

Charlie B100 BOILERS PUMPS Boiler2
type: boiler
type: cur-point
type: his-point
has tag: boiler
has tag: cmd
has tag: cur
has tag: enable
has tag: his
has tag: point
dis: Charlie B100 BOILERS PUMPS Boiler2
enum: false,true
equip ref: Charlie B100 BOILERS PUMPS
kind: Bool
site ref: Charlie
tz: New_York

Charlie B100 BOILERS PUMPS HWP1~2dC
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: his
has tag: hot
has tag: point
has tag: pump
has tag: run
has tag: water
dis: Charlie B100 BOILERS PUMPS HWP1~2dC
enum: On,Off
equip ref: Charlie B100 BOILERS PUMPS
kind: Bool
site ref: Charlie
tz: New_York

Charlie B100 BOILERS PUMPS HWP1~2dS
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: hot
has tag: point
has tag: pump
has tag: run
has tag: sensor
has tag: water
dis: Charlie B100 BOILERS PUMPS HWP1~2dS
enum: Off,On
equip ref: Charlie B100 BOILERS PUMPS
kind: Bool
site ref: Charlie
tz: New_York

Charlie B100 BOILERS PUMPS HWP2~2dC
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: his
has tag: hot
has tag: point
has tag: pump
has tag: run
has tag: water
dis: Charlie B100 BOILERS PUMPS HWP2~2dC
enum: On,Off
equip ref: Charlie B100 BOILERS PUMPS
kind: Bool
site ref: Charlie
tz: New_York

Charlie B100 BOILERS PUMPS HWP2~2dS
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: hot
has tag: point
has tag: pump
has tag: run
has tag: sensor
has tag: water
dis: Charlie B100 BOILERS PUMPS HWP2~2dS
enum: Off,On
equip ref: Charlie B100 BOILERS PUMPS
kind: Bool
site ref: Charlie
tz: New_York

Charlie B100 BOILERS PUMPS HWP3~2dC
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: his
has tag: hot
has tag: point
has tag: pump
has tag: run
has tag: water
dis: Charlie B100 BOILERS PUMPS HWP3~2dC
enum: On,Off
equip ref: Charlie B100 BOILERS PUMPS
kind: Bool
site ref: Charlie
tz: New_York

Charlie B100 BOILERS PUMPS HWP3~2dS
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: hot
has tag: point
has tag: pump
has tag: run
has tag: sensor
has tag: water
dis: Charlie B100 BOILERS PUMPS HWP3~2dS
enum: Off,On
equip ref: Charlie B100 BOILERS PUMPS
kind: Bool
site ref: Charlie
tz: New_York

Charlie B100 BOILERS PUMPS HWR~2dT
type: cur-point
type: his-point
has tag: cur
has tag: entering
has tag: his
has tag: hot
has tag: point
has tag: sensor
has tag: temp
has tag: water
dis: Charlie B100 BOILERS PUMPS HWR~2dT
equip ref: Charlie B100 BOILERS PUMPS
kind: Number
site ref: Charlie
tz: New_York
unit: °F

Charlie B100 BOILERS PUMPS HWS~2dT
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: hot
has tag: leaving
has tag: point
has tag: sensor
has tag: temp
has tag: water
dis: Charlie B100 BOILERS PUMPS HWS~2dT
equip ref: Charlie B100 BOILERS PUMPS
kind: Number
site ref: Charlie
tz: New_York
unit: °F

Charlie B100 BOILERS PUMPS Outside Air Temp Sensor Lockout Setpoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: outside
has tag: point
has tag: sp
has tag: temp
dis: Charlie B100 BOILERS PUMPS Outside Air Temp Sensor Lockout Setpoint
equip ref: Charlie B100 BOILERS PUMPS
kind: Number
site ref: Charlie
tz: New_York
unit: °F
custom: {lockout}

Charlie B100 CHILLER-1
type: chiller
has tag: chiller
has tag: equip
dis: Charlie B100 CHILLER-1
site ref: Charlie
custom: {equipGroup:Chilled Water System}
  equip group: Chilled Water System

Charlie B100 CHILLER-1 CHWR~2dT
type: cur-point
type: his-point
has tag: chilled
has tag: cur
has tag: entering
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: water
dis: Charlie B100 CHILLER-1 CHWR~2dT
equip ref: Charlie B100 CHILLER-1
kind: Number
site ref: Charlie
tz: New_York
unit: °F

Charlie B100 CHILLER-1 CHWS~2dT
type: cur-point
type: his-point
has tag: chilled
has tag: cur
has tag: his
has tag: leaving
has tag: point
has tag: sensor
has tag: temp
has tag: water
dis: Charlie B100 CHILLER-1 CHWS~2dT
equip ref: Charlie B100 CHILLER-1
kind: Number
site ref: Charlie
tz: New_York
unit: °F

Charlie B100 CHILLER-1 Chiler-Override
type: chiller
type: cur-point
type: his-point
has tag: chiller
has tag: cmd
has tag: cur
has tag: enable
has tag: his
has tag: point
dis: Charlie B100 CHILLER-1 Chiler-Override
enum: Off,On
equip ref: Charlie B100 CHILLER-1
kind: Bool
site ref: Charlie
tz: New_York

Charlie B100 CHILLER-1 Chiller-1-Amps
type: cur-point
type: his-point
has tag: cur
has tag: current
has tag: elec
has tag: his
has tag: point
has tag: sensor
dis: Charlie B100 CHILLER-1 Chiller-1-Amps
equip ref: Charlie B100 CHILLER-1
kind: Number
site ref: Charlie
tz: New_York
unit: A
custom: {precision:1}
  precision: 1

Charlie B100 CHILLER-1 Chiller-1-Command
type: chiller
type: cur-point
type: his-point
has tag: chiller
has tag: cmd
has tag: cur
has tag: enable
has tag: his
has tag: point
dis: Charlie B100 CHILLER-1 Chiller-1-Command
enum: Off,On
equip ref: Charlie B100 CHILLER-1
kind: Bool
site ref: Charlie
tz: New_York

Charlie B100 CHILLER-1 OAT-Chiller-Enable-SetPoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: outside
has tag: point
has tag: sp
has tag: temp
dis: Charlie B100 CHILLER-1 OAT-Chiller-Enable-SetPoint
equip ref: Charlie B100 CHILLER-1
kind: Number
site ref: Charlie
tz: New_York
unit: °F

Charlie BLOCK HEAT
type: equip
has tag: equip
dis: Charlie BLOCK HEAT
site ref: Charlie
custom: {equipGroup:Misc}
  equip group: Misc

Charlie BLOCK HEAT Block Temperature
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: hot
has tag: leaving
has tag: point
has tag: sensor
has tag: temp
has tag: water
dis: Charlie BLOCK HEAT Block Temperature
equip ref: Charlie BLOCK HEAT
kind: Number
site ref: Charlie
tz: New_York
unit: °F

Charlie BLOCK HEAT Valve Command
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Charlie BLOCK HEAT Valve Command
equip ref: Charlie BLOCK HEAT
kind: Number
site ref: Charlie
tz: New_York
unit: %

Charlie CHILLER-2
type: chiller
has tag: chiller
has tag: equip
dis: Charlie CHILLER-2
site ref: Charlie
custom: {equipGroup:Chilled Water System}
  equip group: Chilled Water System

Charlie CHILLER-2 CHWR~2dT
type: cur-point
type: his-point
has tag: chilled
has tag: cur
has tag: entering
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: water
dis: Charlie CHILLER-2 CHWR~2dT
equip ref: Charlie CHILLER-2
kind: Number
site ref: Charlie
tz: New_York
unit: °F

Charlie CHILLER-2 CHWS~2dT
type: cur-point
type: his-point
has tag: chilled
has tag: cur
has tag: his
has tag: leaving
has tag: point
has tag: sensor
has tag: temp
has tag: water
dis: Charlie CHILLER-2 CHWS~2dT
equip ref: Charlie CHILLER-2
kind: Number
site ref: Charlie
tz: New_York
unit: °F

Charlie CHILLER-2 Chiler-Override
type: chiller
type: cur-point
type: his-point
has tag: chiller
has tag: cmd
has tag: cur
has tag: enable
has tag: his
has tag: point
dis: Charlie CHILLER-2 Chiler-Override
enum: Off,On
equip ref: Charlie CHILLER-2
kind: Bool
site ref: Charlie
tz: New_York

Charlie CHILLER-2 Chiller-2-Amps
type: cur-point
type: his-point
has tag: cur
has tag: current
has tag: elec
has tag: his
has tag: point
has tag: sensor
dis: Charlie CHILLER-2 Chiller-2-Amps
equip ref: Charlie CHILLER-2
kind: Number
site ref: Charlie
tz: New_York
unit: A
custom: {precision:1}
  precision: 1

Charlie CHILLER-2 Chiller-2-Command
type: chiller
type: cur-point
type: his-point
has tag: chiller
has tag: cmd
has tag: cur
has tag: enable
has tag: his
has tag: point
dis: Charlie CHILLER-2 Chiller-2-Command
enum: Off,On
equip ref: Charlie CHILLER-2
kind: Bool
site ref: Charlie
tz: New_York

Charlie CHILLER-2 OAT-Chiller-Enable-SetPoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: outside
has tag: point
has tag: sp
has tag: temp
dis: Charlie CHILLER-2 OAT-Chiller-Enable-SetPoint
equip ref: Charlie CHILLER-2
kind: Number
site ref: Charlie
tz: New_York
unit: °F

Charlie CWS_Pump1_Meter
type: ac-elec-meter
has tag: ac
has tag: elec
has tag: equip
has tag: meter
dis: Charlie CWS_Pump1_Meter
site ref: Charlie
submeter of: Charlie Elec_Main_100_Meter
custom: {equipGroup:Meters}
  equip group: Meters

Charlie CWS_Pump1_Meter Current Sum Element N
type: cur-point
type: his-point
has tag: cur
has tag: current
has tag: his
has tag: point
has tag: sensor
dis: Charlie CWS_Pump1_Meter Current Sum Element N
equip ref: Charlie CWS_Pump1_Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: A

Charlie CWS_Pump1_Meter Power Demand Peak Element N
type: cur-point
type: his-point
has tag: cur
has tag: elec
has tag: his
has tag: point
has tag: power
has tag: sensor
dis: Charlie CWS_Pump1_Meter Power Demand Peak Element N
equip ref: Charlie CWS_Pump1_Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: kW

Charlie CWS_Pump1_Meter Power Sum Element N
type: cur-point
type: his-point
has tag: cur
has tag: elec
has tag: his
has tag: point
has tag: power
has tag: sensor
dis: Charlie CWS_Pump1_Meter Power Sum Element N
equip ref: Charlie CWS_Pump1_Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: kW

Charlie CWS_Pump1_Meter VA Demand Peak Element N
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: point
has tag: reactive
has tag: sensor
dis: Charlie CWS_Pump1_Meter VA Demand Peak Element N
equip ref: Charlie CWS_Pump1_Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: kVA

Charlie CWS_Pump1_Meter VA Sum Element N
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: point
has tag: reactive
has tag: sensor
dis: Charlie CWS_Pump1_Meter VA Sum Element N
equip ref: Charlie CWS_Pump1_Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: kVA

Charlie CWS_Pump2_Meter
type: ac-elec-meter
has tag: ac
has tag: elec
has tag: equip
has tag: meter
dis: Charlie CWS_Pump2_Meter
site ref: Charlie
submeter of: Charlie Elec_Main_100_Meter
custom: {equipGroup:Meters}
  equip group: Meters

Charlie CWS_Pump2_Meter Current Sum Element C
type: cur-point
type: his-point
has tag: cur
has tag: current
has tag: his
has tag: point
has tag: sensor
dis: Charlie CWS_Pump2_Meter Current Sum Element C
equip ref: Charlie CWS_Pump2_Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: A

Charlie CWS_Pump2_Meter Energy Net Sum Element C
type: cur-point
type: his-point
has tag: cur
has tag: elec
has tag: energy
has tag: his
has tag: point
has tag: sensor
dis: Charlie CWS_Pump2_Meter Energy Net Sum Element C
equip ref: Charlie CWS_Pump2_Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: kWh

Charlie CWS_Pump2_Meter Power Demand Peak Element C
type: cur-point
type: his-point
has tag: cur
has tag: elec
has tag: his
has tag: point
has tag: power
has tag: sensor
dis: Charlie CWS_Pump2_Meter Power Demand Peak Element C
equip ref: Charlie CWS_Pump2_Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: kW

Charlie CWS_Pump2_Meter Power Sum Element C
type: cur-point
type: his-point
has tag: cur
has tag: elec
has tag: his
has tag: point
has tag: power
has tag: sensor
dis: Charlie CWS_Pump2_Meter Power Sum Element C
equip ref: Charlie CWS_Pump2_Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: kW

Charlie CWS_Pump2_Meter VA Demand Peak Element C
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: point
has tag: reactive
has tag: sensor
dis: Charlie CWS_Pump2_Meter VA Demand Peak Element C
equip ref: Charlie CWS_Pump2_Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: kVA

Charlie Chiller1_Meter
type: ac-elec-meter
has tag: ac
has tag: elec
has tag: equip
has tag: meter
dis: Charlie Chiller1_Meter
site ref: Charlie
submeter of: Charlie Elec_Main_100_Meter
custom: {equipGroup:Meters}
  equip group: Meters

Charlie Chiller1_Meter Current Sum Element D
type: cur-point
type: his-point
has tag: cur
has tag: current
has tag: his
has tag: point
has tag: sensor
dis: Charlie Chiller1_Meter Current Sum Element D
equip ref: Charlie Chiller1_Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: A

Charlie Chiller1_Meter Power Demand Peak Element D
type: cur-point
type: his-point
has tag: cur
has tag: elec
has tag: his
has tag: point
has tag: power
has tag: sensor
dis: Charlie Chiller1_Meter Power Demand Peak Element D
equip ref: Charlie Chiller1_Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: kW

Charlie Chiller1_Meter Power Sum Element D
type: cur-point
type: his-point
has tag: cur
has tag: elec
has tag: his
has tag: point
has tag: power
has tag: sensor
dis: Charlie Chiller1_Meter Power Sum Element D
equip ref: Charlie Chiller1_Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: kW

Charlie Chiller1_Meter VA Demand Peak Element D
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: point
has tag: reactive
has tag: sensor
dis: Charlie Chiller1_Meter VA Demand Peak Element D
equip ref: Charlie Chiller1_Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: kVA

Charlie Chiller1_Meter VA Sum Element D
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: point
has tag: reactive
has tag: sensor
dis: Charlie Chiller1_Meter VA Sum Element D
equip ref: Charlie Chiller1_Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: kVA

Charlie Chiller2_Meter
type: ac-elec-meter
has tag: ac
has tag: elec
has tag: equip
has tag: meter
dis: Charlie Chiller2_Meter
site ref: Charlie
submeter of: Charlie Elec_Main_100_Meter
custom: {equipGroup:Meters}
  equip group: Meters

Charlie Chiller2_Meter Current Sum Element H
type: cur-point
type: his-point
has tag: cur
has tag: current
has tag: his
has tag: point
has tag: sensor
dis: Charlie Chiller2_Meter Current Sum Element H
equip ref: Charlie Chiller2_Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: A

Charlie Chiller2_Meter Power Demand Peak Element H
type: cur-point
type: his-point
has tag: cur
has tag: elec
has tag: his
has tag: point
has tag: power
has tag: sensor
dis: Charlie Chiller2_Meter Power Demand Peak Element H
equip ref: Charlie Chiller2_Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: kW

Charlie Chiller2_Meter Power Sum Element H
type: cur-point
type: his-point
has tag: cur
has tag: elec
has tag: his
has tag: point
has tag: power
has tag: sensor
dis: Charlie Chiller2_Meter Power Sum Element H
equip ref: Charlie Chiller2_Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: kW

Charlie Chiller2_Meter VA Demand Peak Element H
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: point
has tag: reactive
has tag: sensor
dis: Charlie Chiller2_Meter VA Demand Peak Element H
equip ref: Charlie Chiller2_Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: kVA

Charlie Chiller2_Meter VA Sum Element H
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: point
has tag: reactive
has tag: sensor
dis: Charlie Chiller2_Meter VA Sum Element H
equip ref: Charlie Chiller2_Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: kVA

Charlie Cooling_Tower_Meter
type: ac-elec-meter
has tag: ac
has tag: elec
has tag: equip
has tag: meter
dis: Charlie Cooling_Tower_Meter
site ref: Charlie
submeter of: Charlie Elec_Main_100_Meter
custom: {equipGroup:Meters}
  equip group: Meters

Charlie Cooling_Tower_Meter Current Sum Element O
type: cur-point
type: his-point
has tag: cur
has tag: current
has tag: his
has tag: point
has tag: sensor
dis: Charlie Cooling_Tower_Meter Current Sum Element O
equip ref: Charlie Cooling_Tower_Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: A

Charlie Cooling_Tower_Meter Power Demand Peak Element O
type: cur-point
type: his-point
has tag: cur
has tag: elec
has tag: his
has tag: point
has tag: power
has tag: sensor
dis: Charlie Cooling_Tower_Meter Power Demand Peak Element O
equip ref: Charlie Cooling_Tower_Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: kW

Charlie Cooling_Tower_Meter Power Sum Element O
type: cur-point
type: his-point
has tag: cur
has tag: elec
has tag: his
has tag: point
has tag: power
has tag: sensor
dis: Charlie Cooling_Tower_Meter Power Sum Element O
equip ref: Charlie Cooling_Tower_Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: kW

Charlie Cooling_Tower_Meter VA Demand Peak Element O
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: point
has tag: reactive
has tag: sensor
dis: Charlie Cooling_Tower_Meter VA Demand Peak Element O
equip ref: Charlie Cooling_Tower_Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: kVA

Charlie Cooling_Tower_Meter VA Sum Element O
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: point
has tag: reactive
has tag: sensor
dis: Charlie Cooling_Tower_Meter VA Sum Element O
equip ref: Charlie Cooling_Tower_Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: kVA

Charlie East_Return_Fan_Meter
type: ac-elec-meter
has tag: ac
has tag: elec
has tag: equip
has tag: meter
air ref: Charlie AHU 1
dis: Charlie East_Return_Fan_Meter
equip ref: Charlie AHU 1
site ref: Charlie
submeter of: Charlie Elec_Main_100_Meter
custom: {equipGroup:Meters}
  equip group: Meters

Charlie East_Return_Fan_Meter Current Sum Element K
type: cur-point
type: his-point
has tag: cur
has tag: current
has tag: his
has tag: point
has tag: sensor
dis: Charlie East_Return_Fan_Meter Current Sum Element K
equip ref: Charlie East_Return_Fan_Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: A

Charlie East_Return_Fan_Meter Power Demand Peak Element K
type: cur-point
type: his-point
has tag: ac
has tag: cur
has tag: demand
has tag: elec
has tag: his
has tag: point
has tag: power
has tag: sensor
dis: Charlie East_Return_Fan_Meter Power Demand Peak Element K
equip ref: Charlie East_Return_Fan_Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: kW

Charlie East_Return_Fan_Meter Power Sum Element K
type: cur-point
type: his-point
has tag: ac
has tag: cur
has tag: elec
has tag: his
has tag: point
has tag: power
has tag: sensor
dis: Charlie East_Return_Fan_Meter Power Sum Element K
equip ref: Charlie East_Return_Fan_Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: kW

Charlie East_Return_Fan_Meter VA Demand Peak Element K
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: point
has tag: reactive
has tag: sensor
dis: Charlie East_Return_Fan_Meter VA Demand Peak Element K
equip ref: Charlie East_Return_Fan_Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: kVA

Charlie East_Return_Fan_Meter VA Sum Element K
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: point
has tag: reactive
has tag: sensor
dis: Charlie East_Return_Fan_Meter VA Sum Element K
equip ref: Charlie East_Return_Fan_Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: kVA

Charlie East_Supply_Fan_Meter
type: ac-elec-meter
has tag: ac
has tag: elec
has tag: equip
has tag: meter
air ref: Charlie AHU 1
dis: Charlie East_Supply_Fan_Meter
equip ref: Charlie AHU 1
site ref: Charlie
submeter of: Charlie Elec_Main_100_Meter
custom: {equipGroup:Meters}
  equip group: Meters

Charlie East_Supply_Fan_Meter Current Sum Element L
type: cur-point
type: his-point
has tag: cur
has tag: current
has tag: his
has tag: point
has tag: sensor
dis: Charlie East_Supply_Fan_Meter Current Sum Element L
equip ref: Charlie East_Supply_Fan_Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: A

Charlie East_Supply_Fan_Meter Power Demand Peak Element L
type: cur-point
type: his-point
has tag: ac
has tag: cur
has tag: demand
has tag: elec
has tag: his
has tag: point
has tag: power
has tag: sensor
dis: Charlie East_Supply_Fan_Meter Power Demand Peak Element L
equip ref: Charlie East_Supply_Fan_Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: kW

Charlie East_Supply_Fan_Meter Power Sum Element L
type: cur-point
type: his-point
has tag: ac
has tag: cur
has tag: elec
has tag: his
has tag: point
has tag: power
has tag: sensor
dis: Charlie East_Supply_Fan_Meter Power Sum Element L
equip ref: Charlie East_Supply_Fan_Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: kW

Charlie East_Supply_Fan_Meter VA Demand Peak Element L
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: point
has tag: reactive
has tag: sensor
dis: Charlie East_Supply_Fan_Meter VA Demand Peak Element L
equip ref: Charlie East_Supply_Fan_Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: kVA

Charlie East_Supply_Fan_Meter VA Sum Element L
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: point
has tag: reactive
has tag: sensor
dis: Charlie East_Supply_Fan_Meter VA Sum Element L
equip ref: Charlie East_Supply_Fan_Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: kVA

Charlie Elec_Main_100_Meter
type: ac-elec-meter
has tag: ac
has tag: elec
has tag: equip
has tag: meter
has tag: siteMeter
dis: Charlie Elec_Main_100_Meter
site ref: Charlie
custom: {equipGroup:Meters}
  equip group: Meters

Charlie Elec_Main_100_Meter kW System
type: cur-point
type: his-point
has tag: ac
has tag: cur
has tag: demand
has tag: elec
has tag: his
has tag: point
has tag: power
has tag: sensor
dis: Charlie Elec_Main_100_Meter kW System
equip ref: Charlie Elec_Main_100_Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: kW

Charlie Elec_Main_100_Meter kWh System Total
type: cur-point
type: his-point
has tag: ac
has tag: cur
has tag: elec
has tag: energy
has tag: his
has tag: hisTotalized
has tag: point
has tag: sensor
dis: Charlie Elec_Main_100_Meter kWh System Total
equip ref: Charlie Elec_Main_100_Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: kWh
custom: {pointType:}

Charlie Floor-4 400L-Meter
type: ac-elec-meter
has tag: ac
has tag: elec
has tag: equip
has tag: meter
dis: Charlie Floor-4 400L-Meter
site ref: Charlie
submeter of: Charlie Elec_Main_100_Meter
custom: {equipGroup:Meters}
  equip group: Meters

Charlie Floor-4 400L-Meter Energy Total
type: cur-point
type: his-point
has tag: cur
has tag: elec
has tag: energy
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 400L-Meter Energy Total
equip ref: Charlie Floor-4 400L-Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: kWh

Charlie Floor-4 400L-Meter Line Voltage AB
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 400L-Meter Line Voltage AB
equip ref: Charlie Floor-4 400L-Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: V

Charlie Floor-4 400L-Meter Line Voltage BC
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 400L-Meter Line Voltage BC
equip ref: Charlie Floor-4 400L-Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: V

Charlie Floor-4 400L-Meter Line Voltage CA
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 400L-Meter Line Voltage CA
equip ref: Charlie Floor-4 400L-Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: V

Charlie Floor-4 400L-Meter Total Active Power
type: cur-point
type: his-point
has tag: cur
has tag: elec
has tag: his
has tag: point
has tag: power
has tag: sensor
dis: Charlie Floor-4 400L-Meter Total Active Power
equip ref: Charlie Floor-4 400L-Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: kW

Charlie Floor-4 400R-Meter
type: ac-elec-meter
has tag: ac
has tag: elec
has tag: equip
has tag: meter
dis: Charlie Floor-4 400R-Meter
site ref: Charlie
submeter of: Charlie Elec_Main_100_Meter
custom: {equipGroup:Meters}
  equip group: Meters

Charlie Floor-4 400R-Meter Energy Total
type: cur-point
type: his-point
has tag: cur
has tag: elec
has tag: energy
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 400R-Meter Energy Total
equip ref: Charlie Floor-4 400R-Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: kWh

Charlie Floor-4 400R-Meter Line Voltage AB
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 400R-Meter Line Voltage AB
equip ref: Charlie Floor-4 400R-Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: V

Charlie Floor-4 400R-Meter Line Voltage BC
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 400R-Meter Line Voltage BC
equip ref: Charlie Floor-4 400R-Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: V

Charlie Floor-4 400R-Meter Line Voltage CA
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 400R-Meter Line Voltage CA
equip ref: Charlie Floor-4 400R-Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: V

Charlie Floor-4 400R-Meter Offline Meter
type: his-point
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 400R-Meter Offline Meter
equip ref: Charlie Floor-4 400R-Meter
kind: Number
site ref: Charlie
tz: Detroit
custom: {offlineMeter}

Charlie Floor-4 400R-Meter Total Active Power
type: cur-point
type: his-point
has tag: cur
has tag: elec
has tag: his
has tag: point
has tag: power
has tag: sensor
dis: Charlie Floor-4 400R-Meter Total Active Power
equip ref: Charlie Floor-4 400R-Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: kW

Charlie Floor-4 VAV_1
type: vav
has tag: equip
has tag: vav
dis: Charlie Floor-4 VAV_1
site ref: Charlie
custom: {equipGroup:VAVs}
  equip group: VAVs

Charlie Floor-4 VAV_1 dpr_pos
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: damper
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_1 dpr_pos
equip ref: Charlie Floor-4 VAV_1
kind: Number
site ref: Charlie
tz: Detroit
unit: %

Charlie Floor-4 VAV_1 eff_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: effective
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_1 eff_cl_stpt
equip ref: Charlie Floor-4 VAV_1
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_1 eff_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: effective
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_1 eff_ht_stpt
equip ref: Charlie Floor-4 VAV_1
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_1 flow_input
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_1 flow_input
equip ref: Charlie Floor-4 VAV_1
kind: Number
max val: 96
min val: 45
site ref: Charlie
tz: Detroit
unit: cfm
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_1 hw_valve
type: cur-point
type: his-point
has tag: cur
has tag: heat
has tag: his
has tag: point
has tag: sensor
has tag: valve
dis: Charlie Floor-4 VAV_1 hw_valve
equip ref: Charlie Floor-4 VAV_1
kind: Number
max val: 100
min val: 0
site ref: Charlie
tz: Detroit
unit: %
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_1 link_ahu_mode
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_1 link_ahu_mode
enum: OFF,WARM$2dUP,HEAT,COOL,FREECOOL,PRESSURIZE,EVACUATE,VENT
equip ref: Charlie Floor-4 VAV_1
kind: Str
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_1 occ_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_1 occ_cl_stpt
equip ref: Charlie Floor-4 VAV_1
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_1 occ_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_1 occ_ht_stpt
equip ref: Charlie Floor-4 VAV_1
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_1 occ_status
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: his
has tag: occupied
has tag: point
dis: Charlie Floor-4 VAV_1 occ_status
enum: Unoccupied,Occupied
equip ref: Charlie Floor-4 VAV_1
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_1 occ_switch
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: occupied
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_1 occ_switch
enum: Open,Closed
equip ref: Charlie Floor-4 VAV_1
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_1 sa_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Charlie Floor-4 VAV_1 sa_temp
equip ref: Charlie Floor-4 VAV_1
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_1 space_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_1 space_temp
equip ref: Charlie Floor-4 VAV_1
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_1 terminal_status
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_1 terminal_status
enum: Off,Heating,Warm$2dUp,Vent,N$2fA,Cooling,Dehumidify,Reheat,Pressurize,Evacuate,Shutdown,IAQ$20Override,Air$20Balancing
equip ref: Charlie Floor-4 VAV_1
kind: Str
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_1 unocc_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_1 unocc_cl_stpt
equip ref: Charlie Floor-4 VAV_1
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_1 unocc_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_1 unocc_ht_stpt
equip ref: Charlie Floor-4 VAV_1
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_10
type: vav
has tag: equip
has tag: vav
dis: Charlie Floor-4 VAV_10
site ref: Charlie
custom: {equipGroup:VAVs}
  equip group: VAVs

Charlie Floor-4 VAV_10 dpr_pos
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: damper
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_10 dpr_pos
equip ref: Charlie Floor-4 VAV_10
kind: Number
site ref: Charlie
tz: Detroit
unit: %

Charlie Floor-4 VAV_10 eff_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: effective
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_10 eff_cl_stpt
equip ref: Charlie Floor-4 VAV_10
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_10 eff_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: effective
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_10 eff_ht_stpt
equip ref: Charlie Floor-4 VAV_10
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_10 flow_input
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_10 flow_input
equip ref: Charlie Floor-4 VAV_10
kind: Number
max val: 96
min val: 45
site ref: Charlie
tz: Detroit
unit: cfm
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_10 hw_valve
type: cur-point
type: his-point
has tag: cur
has tag: heat
has tag: his
has tag: point
has tag: sensor
has tag: valve
dis: Charlie Floor-4 VAV_10 hw_valve
equip ref: Charlie Floor-4 VAV_10
kind: Number
max val: 100
min val: 0
site ref: Charlie
tz: Detroit
unit: %
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_10 occ_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_10 occ_cl_stpt
equip ref: Charlie Floor-4 VAV_10
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_10 occ_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_10 occ_ht_stpt
equip ref: Charlie Floor-4 VAV_10
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_10 occ_status
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: his
has tag: occupied
has tag: point
dis: Charlie Floor-4 VAV_10 occ_status
enum: Unoccupied,Occupied
equip ref: Charlie Floor-4 VAV_10
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_10 occ_switch
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: occupied
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_10 occ_switch
enum: Open,Closed
equip ref: Charlie Floor-4 VAV_10
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_10 sa_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Charlie Floor-4 VAV_10 sa_temp
equip ref: Charlie Floor-4 VAV_10
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_10 space_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_10 space_temp
equip ref: Charlie Floor-4 VAV_10
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_10 unocc_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_10 unocc_cl_stpt
equip ref: Charlie Floor-4 VAV_10
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_10 unocc_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_10 unocc_ht_stpt
equip ref: Charlie Floor-4 VAV_10
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_11
type: vav
has tag: equip
has tag: vav
dis: Charlie Floor-4 VAV_11
site ref: Charlie
custom: {equipGroup:VAVs}
  equip group: VAVs

Charlie Floor-4 VAV_11 dpr_pos
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: damper
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_11 dpr_pos
equip ref: Charlie Floor-4 VAV_11
kind: Number
site ref: Charlie
tz: Detroit
unit: %

Charlie Floor-4 VAV_11 eff_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: effective
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_11 eff_cl_stpt
equip ref: Charlie Floor-4 VAV_11
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_11 eff_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: effective
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_11 eff_ht_stpt
equip ref: Charlie Floor-4 VAV_11
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_11 flow_input
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_11 flow_input
equip ref: Charlie Floor-4 VAV_11
kind: Number
max val: 96
min val: 45
site ref: Charlie
tz: Detroit
unit: cfm
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_11 hw_valve
type: cur-point
type: his-point
has tag: cur
has tag: heat
has tag: his
has tag: point
has tag: sensor
has tag: valve
dis: Charlie Floor-4 VAV_11 hw_valve
equip ref: Charlie Floor-4 VAV_11
kind: Number
max val: 100
min val: 0
site ref: Charlie
tz: Detroit
unit: %
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_11 occ_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_11 occ_cl_stpt
equip ref: Charlie Floor-4 VAV_11
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_11 occ_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_11 occ_ht_stpt
equip ref: Charlie Floor-4 VAV_11
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_11 occ_status
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: his
has tag: occupied
has tag: point
dis: Charlie Floor-4 VAV_11 occ_status
enum: Unoccupied,Occupied
equip ref: Charlie Floor-4 VAV_11
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_11 occ_switch
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: occupied
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_11 occ_switch
enum: Open,Closed
equip ref: Charlie Floor-4 VAV_11
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_11 sa_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Charlie Floor-4 VAV_11 sa_temp
equip ref: Charlie Floor-4 VAV_11
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_11 space_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_11 space_temp
equip ref: Charlie Floor-4 VAV_11
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_11 unocc_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_11 unocc_cl_stpt
equip ref: Charlie Floor-4 VAV_11
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_11 unocc_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_11 unocc_ht_stpt
equip ref: Charlie Floor-4 VAV_11
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_12
type: vav
has tag: equip
has tag: vav
dis: Charlie Floor-4 VAV_12
site ref: Charlie
custom: {equipGroup:VAVs}
  equip group: VAVs

Charlie Floor-4 VAV_12 dpr_pos
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: damper
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_12 dpr_pos
equip ref: Charlie Floor-4 VAV_12
kind: Number
site ref: Charlie
tz: Detroit
unit: %

Charlie Floor-4 VAV_12 eff_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: effective
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_12 eff_cl_stpt
equip ref: Charlie Floor-4 VAV_12
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_12 eff_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: effective
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_12 eff_ht_stpt
equip ref: Charlie Floor-4 VAV_12
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_12 flow_input
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_12 flow_input
equip ref: Charlie Floor-4 VAV_12
kind: Number
max val: 96
min val: 45
site ref: Charlie
tz: Detroit
unit: cfm
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_12 hw_valve
type: cur-point
type: his-point
has tag: cur
has tag: heat
has tag: his
has tag: point
has tag: sensor
has tag: valve
dis: Charlie Floor-4 VAV_12 hw_valve
equip ref: Charlie Floor-4 VAV_12
kind: Number
max val: 100
min val: 0
site ref: Charlie
tz: Detroit
unit: %
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_12 occ_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_12 occ_cl_stpt
equip ref: Charlie Floor-4 VAV_12
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_12 occ_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_12 occ_ht_stpt
equip ref: Charlie Floor-4 VAV_12
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_12 occ_status
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: his
has tag: occupied
has tag: point
dis: Charlie Floor-4 VAV_12 occ_status
enum: Unoccupied,Occupied
equip ref: Charlie Floor-4 VAV_12
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_12 occ_switch
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: occupied
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_12 occ_switch
enum: Open,Closed
equip ref: Charlie Floor-4 VAV_12
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_12 sa_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Charlie Floor-4 VAV_12 sa_temp
equip ref: Charlie Floor-4 VAV_12
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_12 space_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_12 space_temp
equip ref: Charlie Floor-4 VAV_12
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_12 unocc_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_12 unocc_cl_stpt
equip ref: Charlie Floor-4 VAV_12
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_12 unocc_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_12 unocc_ht_stpt
equip ref: Charlie Floor-4 VAV_12
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_13
type: vav
has tag: equip
has tag: vav
dis: Charlie Floor-4 VAV_13
site ref: Charlie
custom: {equipGroup:VAVs}
  equip group: VAVs

Charlie Floor-4 VAV_13 dpr_pos
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: damper
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_13 dpr_pos
equip ref: Charlie Floor-4 VAV_13
kind: Number
site ref: Charlie
tz: Detroit
unit: %

Charlie Floor-4 VAV_13 eff_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: effective
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_13 eff_cl_stpt
equip ref: Charlie Floor-4 VAV_13
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_13 eff_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: effective
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_13 eff_ht_stpt
equip ref: Charlie Floor-4 VAV_13
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_13 flow_input
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_13 flow_input
equip ref: Charlie Floor-4 VAV_13
kind: Number
max val: 96
min val: 45
site ref: Charlie
tz: Detroit
unit: cfm
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_13 hw_valve
type: cur-point
type: his-point
has tag: cur
has tag: heat
has tag: his
has tag: point
has tag: sensor
has tag: valve
dis: Charlie Floor-4 VAV_13 hw_valve
equip ref: Charlie Floor-4 VAV_13
kind: Number
max val: 100
min val: 0
site ref: Charlie
tz: Detroit
unit: %
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_13 occ_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_13 occ_cl_stpt
equip ref: Charlie Floor-4 VAV_13
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_13 occ_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_13 occ_ht_stpt
equip ref: Charlie Floor-4 VAV_13
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_13 occ_status
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: his
has tag: occupied
has tag: point
dis: Charlie Floor-4 VAV_13 occ_status
enum: Unoccupied,Occupied
equip ref: Charlie Floor-4 VAV_13
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_13 occ_switch
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: occupied
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_13 occ_switch
enum: Open,Closed
equip ref: Charlie Floor-4 VAV_13
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_13 sa_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Charlie Floor-4 VAV_13 sa_temp
equip ref: Charlie Floor-4 VAV_13
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_13 space_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_13 space_temp
equip ref: Charlie Floor-4 VAV_13
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_13 unocc_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_13 unocc_cl_stpt
equip ref: Charlie Floor-4 VAV_13
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_13 unocc_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_13 unocc_ht_stpt
equip ref: Charlie Floor-4 VAV_13
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_14
type: vav
has tag: equip
has tag: vav
dis: Charlie Floor-4 VAV_14
site ref: Charlie
custom: {equipGroup:VAVs}
  equip group: VAVs

Charlie Floor-4 VAV_14 dpr_pos
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: damper
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_14 dpr_pos
equip ref: Charlie Floor-4 VAV_14
kind: Number
site ref: Charlie
tz: Detroit
unit: %

Charlie Floor-4 VAV_14 eff_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: effective
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_14 eff_cl_stpt
equip ref: Charlie Floor-4 VAV_14
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_14 eff_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: effective
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_14 eff_ht_stpt
equip ref: Charlie Floor-4 VAV_14
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_14 flow_input
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_14 flow_input
equip ref: Charlie Floor-4 VAV_14
kind: Number
max val: 96
min val: 45
site ref: Charlie
tz: Detroit
unit: cfm
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_14 hw_valve
type: cur-point
type: his-point
has tag: cur
has tag: heat
has tag: his
has tag: point
has tag: sensor
has tag: valve
dis: Charlie Floor-4 VAV_14 hw_valve
equip ref: Charlie Floor-4 VAV_14
kind: Number
max val: 100
min val: 0
site ref: Charlie
tz: Detroit
unit: %
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_14 occ_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_14 occ_cl_stpt
equip ref: Charlie Floor-4 VAV_14
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_14 occ_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_14 occ_ht_stpt
equip ref: Charlie Floor-4 VAV_14
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_14 occ_status
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: his
has tag: occupied
has tag: point
dis: Charlie Floor-4 VAV_14 occ_status
enum: Unoccupied,Occupied
equip ref: Charlie Floor-4 VAV_14
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_14 occ_switch
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: occupied
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_14 occ_switch
enum: Open,Closed
equip ref: Charlie Floor-4 VAV_14
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_14 sa_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Charlie Floor-4 VAV_14 sa_temp
equip ref: Charlie Floor-4 VAV_14
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_14 space_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_14 space_temp
equip ref: Charlie Floor-4 VAV_14
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_14 unocc_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_14 unocc_cl_stpt
equip ref: Charlie Floor-4 VAV_14
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_14 unocc_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_14 unocc_ht_stpt
equip ref: Charlie Floor-4 VAV_14
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_15
type: vav
has tag: equip
has tag: vav
dis: Charlie Floor-4 VAV_15
site ref: Charlie
custom: {equipGroup:VAVs}
  equip group: VAVs

Charlie Floor-4 VAV_15 dpr_pos
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: damper
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_15 dpr_pos
equip ref: Charlie Floor-4 VAV_15
kind: Number
site ref: Charlie
tz: Detroit
unit: %

Charlie Floor-4 VAV_15 eff_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: effective
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_15 eff_cl_stpt
equip ref: Charlie Floor-4 VAV_15
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_15 eff_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: effective
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_15 eff_ht_stpt
equip ref: Charlie Floor-4 VAV_15
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_15 flow_input
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_15 flow_input
equip ref: Charlie Floor-4 VAV_15
kind: Number
max val: 96
min val: 45
site ref: Charlie
tz: Detroit
unit: cfm
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_15 hw_valve
type: cur-point
type: his-point
has tag: cur
has tag: heat
has tag: his
has tag: point
has tag: sensor
has tag: valve
dis: Charlie Floor-4 VAV_15 hw_valve
equip ref: Charlie Floor-4 VAV_15
kind: Number
max val: 100
min val: 0
site ref: Charlie
tz: Detroit
unit: %
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_15 occ_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_15 occ_cl_stpt
equip ref: Charlie Floor-4 VAV_15
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_15 occ_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_15 occ_ht_stpt
equip ref: Charlie Floor-4 VAV_15
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_15 occ_status
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: his
has tag: occupied
has tag: point
dis: Charlie Floor-4 VAV_15 occ_status
enum: Unoccupied,Occupied
equip ref: Charlie Floor-4 VAV_15
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_15 occ_switch
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: occupied
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_15 occ_switch
enum: Open,Closed
equip ref: Charlie Floor-4 VAV_15
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_15 sa_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Charlie Floor-4 VAV_15 sa_temp
equip ref: Charlie Floor-4 VAV_15
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_15 space_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_15 space_temp
equip ref: Charlie Floor-4 VAV_15
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_15 unocc_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_15 unocc_cl_stpt
equip ref: Charlie Floor-4 VAV_15
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_15 unocc_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_15 unocc_ht_stpt
equip ref: Charlie Floor-4 VAV_15
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_16
type: vav
has tag: equip
has tag: vav
dis: Charlie Floor-4 VAV_16
site ref: Charlie
custom: {equipGroup:VAVs}
  equip group: VAVs

Charlie Floor-4 VAV_16 dpr_pos
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: damper
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_16 dpr_pos
equip ref: Charlie Floor-4 VAV_16
kind: Number
site ref: Charlie
tz: Detroit
unit: %

Charlie Floor-4 VAV_16 eff_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: effective
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_16 eff_cl_stpt
equip ref: Charlie Floor-4 VAV_16
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_16 eff_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: effective
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_16 eff_ht_stpt
equip ref: Charlie Floor-4 VAV_16
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_16 flow_input
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_16 flow_input
equip ref: Charlie Floor-4 VAV_16
kind: Number
max val: 96
min val: 45
site ref: Charlie
tz: Detroit
unit: cfm
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_16 hw_valve
type: cur-point
type: his-point
has tag: cur
has tag: heat
has tag: his
has tag: point
has tag: sensor
has tag: valve
dis: Charlie Floor-4 VAV_16 hw_valve
equip ref: Charlie Floor-4 VAV_16
kind: Number
max val: 100
min val: 0
site ref: Charlie
tz: Detroit
unit: %
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_16 occ_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_16 occ_cl_stpt
equip ref: Charlie Floor-4 VAV_16
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_16 occ_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_16 occ_ht_stpt
equip ref: Charlie Floor-4 VAV_16
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_16 occ_status
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: his
has tag: occupied
has tag: point
dis: Charlie Floor-4 VAV_16 occ_status
enum: Unoccupied,Occupied
equip ref: Charlie Floor-4 VAV_16
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_16 occ_switch
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: occupied
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_16 occ_switch
enum: Open,Closed
equip ref: Charlie Floor-4 VAV_16
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_16 sa_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Charlie Floor-4 VAV_16 sa_temp
equip ref: Charlie Floor-4 VAV_16
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_16 space_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_16 space_temp
equip ref: Charlie Floor-4 VAV_16
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_16 unocc_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_16 unocc_cl_stpt
equip ref: Charlie Floor-4 VAV_16
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_16 unocc_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_16 unocc_ht_stpt
equip ref: Charlie Floor-4 VAV_16
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_17
type: vav
has tag: equip
has tag: vav
dis: Charlie Floor-4 VAV_17
site ref: Charlie
custom: {equipGroup:VAVs}
  equip group: VAVs

Charlie Floor-4 VAV_17 dpr_pos
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: damper
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_17 dpr_pos
equip ref: Charlie Floor-4 VAV_17
kind: Number
site ref: Charlie
tz: Detroit
unit: %

Charlie Floor-4 VAV_17 eff_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: effective
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_17 eff_cl_stpt
equip ref: Charlie Floor-4 VAV_17
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_17 eff_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: effective
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_17 eff_ht_stpt
equip ref: Charlie Floor-4 VAV_17
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_17 flow_input
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_17 flow_input
equip ref: Charlie Floor-4 VAV_17
kind: Number
max val: 96
min val: 45
site ref: Charlie
tz: Detroit
unit: cfm
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_17 hw_valve
type: cur-point
type: his-point
has tag: cur
has tag: heat
has tag: his
has tag: point
has tag: sensor
has tag: valve
dis: Charlie Floor-4 VAV_17 hw_valve
equip ref: Charlie Floor-4 VAV_17
kind: Number
max val: 100
min val: 0
site ref: Charlie
tz: Detroit
unit: %
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_17 occ_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_17 occ_cl_stpt
equip ref: Charlie Floor-4 VAV_17
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_17 occ_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_17 occ_ht_stpt
equip ref: Charlie Floor-4 VAV_17
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_17 occ_status
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: his
has tag: occupied
has tag: point
dis: Charlie Floor-4 VAV_17 occ_status
enum: Unoccupied,Occupied
equip ref: Charlie Floor-4 VAV_17
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_17 occ_switch
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: occupied
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_17 occ_switch
enum: Open,Closed
equip ref: Charlie Floor-4 VAV_17
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_17 sa_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Charlie Floor-4 VAV_17 sa_temp
equip ref: Charlie Floor-4 VAV_17
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_17 space_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_17 space_temp
equip ref: Charlie Floor-4 VAV_17
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_17 unocc_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_17 unocc_cl_stpt
equip ref: Charlie Floor-4 VAV_17
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_17 unocc_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_17 unocc_ht_stpt
equip ref: Charlie Floor-4 VAV_17
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_18
type: vav
has tag: equip
has tag: vav
dis: Charlie Floor-4 VAV_18
site ref: Charlie
custom: {equipGroup:VAVs}
  equip group: VAVs

Charlie Floor-4 VAV_18 dpr_pos
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: damper
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_18 dpr_pos
equip ref: Charlie Floor-4 VAV_18
kind: Number
site ref: Charlie
tz: Detroit
unit: %

Charlie Floor-4 VAV_18 eff_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: effective
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_18 eff_cl_stpt
equip ref: Charlie Floor-4 VAV_18
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_18 eff_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: effective
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_18 eff_ht_stpt
equip ref: Charlie Floor-4 VAV_18
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_18 flow_input
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_18 flow_input
equip ref: Charlie Floor-4 VAV_18
kind: Number
max val: 96
min val: 45
site ref: Charlie
tz: Detroit
unit: cfm
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_18 hw_valve
type: cur-point
type: his-point
has tag: cur
has tag: heat
has tag: his
has tag: point
has tag: sensor
has tag: valve
dis: Charlie Floor-4 VAV_18 hw_valve
equip ref: Charlie Floor-4 VAV_18
kind: Number
max val: 100
min val: 0
site ref: Charlie
tz: Detroit
unit: %
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_18 occ_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_18 occ_cl_stpt
equip ref: Charlie Floor-4 VAV_18
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_18 occ_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_18 occ_ht_stpt
equip ref: Charlie Floor-4 VAV_18
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_18 occ_status
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: his
has tag: occupied
has tag: point
dis: Charlie Floor-4 VAV_18 occ_status
enum: Unoccupied,Occupied
equip ref: Charlie Floor-4 VAV_18
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_18 occ_switch
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: occupied
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_18 occ_switch
enum: Open,Closed
equip ref: Charlie Floor-4 VAV_18
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_18 sa_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Charlie Floor-4 VAV_18 sa_temp
equip ref: Charlie Floor-4 VAV_18
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_18 space_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_18 space_temp
equip ref: Charlie Floor-4 VAV_18
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_18 unocc_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_18 unocc_cl_stpt
equip ref: Charlie Floor-4 VAV_18
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_18 unocc_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_18 unocc_ht_stpt
equip ref: Charlie Floor-4 VAV_18
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_19
type: vav
has tag: equip
has tag: vav
dis: Charlie Floor-4 VAV_19
site ref: Charlie
custom: {equipGroup:VAVs}
  equip group: VAVs

Charlie Floor-4 VAV_19 dpr_pos
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: damper
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_19 dpr_pos
equip ref: Charlie Floor-4 VAV_19
kind: Number
site ref: Charlie
tz: Detroit
unit: %

Charlie Floor-4 VAV_19 eff_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: effective
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_19 eff_cl_stpt
equip ref: Charlie Floor-4 VAV_19
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_19 eff_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: effective
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_19 eff_ht_stpt
equip ref: Charlie Floor-4 VAV_19
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_19 flow_input
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_19 flow_input
equip ref: Charlie Floor-4 VAV_19
kind: Number
max val: 96
min val: 45
site ref: Charlie
tz: Detroit
unit: cfm
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_19 hw_valve
type: cur-point
type: his-point
has tag: cur
has tag: heat
has tag: his
has tag: point
has tag: sensor
has tag: valve
dis: Charlie Floor-4 VAV_19 hw_valve
equip ref: Charlie Floor-4 VAV_19
kind: Number
max val: 100
min val: 0
site ref: Charlie
tz: Detroit
unit: %
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_19 occ_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_19 occ_cl_stpt
equip ref: Charlie Floor-4 VAV_19
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_19 occ_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_19 occ_ht_stpt
equip ref: Charlie Floor-4 VAV_19
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_19 occ_status
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: his
has tag: occupied
has tag: point
dis: Charlie Floor-4 VAV_19 occ_status
enum: Unoccupied,Occupied
equip ref: Charlie Floor-4 VAV_19
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_19 occ_switch
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: occupied
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_19 occ_switch
enum: Open,Closed
equip ref: Charlie Floor-4 VAV_19
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_19 sa_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Charlie Floor-4 VAV_19 sa_temp
equip ref: Charlie Floor-4 VAV_19
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_19 space_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_19 space_temp
equip ref: Charlie Floor-4 VAV_19
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_19 unocc_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_19 unocc_cl_stpt
equip ref: Charlie Floor-4 VAV_19
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_19 unocc_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_19 unocc_ht_stpt
equip ref: Charlie Floor-4 VAV_19
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_2
type: vav
has tag: equip
has tag: vav
dis: Charlie Floor-4 VAV_2
site ref: Charlie
custom: {equipGroup:VAVs}
  equip group: VAVs

Charlie Floor-4 VAV_2 dpr_pos
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: damper
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_2 dpr_pos
equip ref: Charlie Floor-4 VAV_2
kind: Number
site ref: Charlie
tz: Detroit
unit: %

Charlie Floor-4 VAV_2 eff_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: effective
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_2 eff_cl_stpt
equip ref: Charlie Floor-4 VAV_2
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_2 eff_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: effective
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_2 eff_ht_stpt
equip ref: Charlie Floor-4 VAV_2
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_2 flow_input
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_2 flow_input
equip ref: Charlie Floor-4 VAV_2
kind: Number
max val: 96
min val: 45
site ref: Charlie
tz: Detroit
unit: cfm
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_2 hw_valve
type: cur-point
type: his-point
has tag: cur
has tag: heat
has tag: his
has tag: point
has tag: sensor
has tag: valve
dis: Charlie Floor-4 VAV_2 hw_valve
equip ref: Charlie Floor-4 VAV_2
kind: Number
max val: 100
min val: 0
site ref: Charlie
tz: Detroit
unit: %
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_2 occ_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_2 occ_cl_stpt
equip ref: Charlie Floor-4 VAV_2
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_2 occ_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_2 occ_ht_stpt
equip ref: Charlie Floor-4 VAV_2
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_2 occ_status
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: his
has tag: occupied
has tag: point
dis: Charlie Floor-4 VAV_2 occ_status
enum: Unoccupied,Occupied
equip ref: Charlie Floor-4 VAV_2
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_2 occ_switch
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: occupied
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_2 occ_switch
enum: Open,Closed
equip ref: Charlie Floor-4 VAV_2
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_2 sa_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Charlie Floor-4 VAV_2 sa_temp
equip ref: Charlie Floor-4 VAV_2
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_2 space_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_2 space_temp
equip ref: Charlie Floor-4 VAV_2
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_2 unocc_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_2 unocc_cl_stpt
equip ref: Charlie Floor-4 VAV_2
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_2 unocc_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_2 unocc_ht_stpt
equip ref: Charlie Floor-4 VAV_2
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_20
type: vav
has tag: equip
has tag: vav
dis: Charlie Floor-4 VAV_20
site ref: Charlie
custom: {equipGroup:VAVs}
  equip group: VAVs

Charlie Floor-4 VAV_20 dpr_pos
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: damper
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_20 dpr_pos
equip ref: Charlie Floor-4 VAV_20
kind: Number
site ref: Charlie
tz: Detroit
unit: %

Charlie Floor-4 VAV_20 eff_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: effective
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_20 eff_cl_stpt
equip ref: Charlie Floor-4 VAV_20
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_20 eff_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: effective
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_20 eff_ht_stpt
equip ref: Charlie Floor-4 VAV_20
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_20 flow_input
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_20 flow_input
equip ref: Charlie Floor-4 VAV_20
kind: Number
max val: 96
min val: 45
site ref: Charlie
tz: Detroit
unit: cfm
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_20 hw_valve
type: cur-point
type: his-point
has tag: cur
has tag: heat
has tag: his
has tag: point
has tag: sensor
has tag: valve
dis: Charlie Floor-4 VAV_20 hw_valve
equip ref: Charlie Floor-4 VAV_20
kind: Number
max val: 100
min val: 0
site ref: Charlie
tz: Detroit
unit: %
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_20 occ_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_20 occ_cl_stpt
equip ref: Charlie Floor-4 VAV_20
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_20 occ_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_20 occ_ht_stpt
equip ref: Charlie Floor-4 VAV_20
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_20 occ_status
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: his
has tag: occupied
has tag: point
dis: Charlie Floor-4 VAV_20 occ_status
enum: Unoccupied,Occupied
equip ref: Charlie Floor-4 VAV_20
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_20 occ_switch
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: occupied
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_20 occ_switch
enum: Open,Closed
equip ref: Charlie Floor-4 VAV_20
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_20 sa_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Charlie Floor-4 VAV_20 sa_temp
equip ref: Charlie Floor-4 VAV_20
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_20 space_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_20 space_temp
equip ref: Charlie Floor-4 VAV_20
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_20 unocc_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_20 unocc_cl_stpt
equip ref: Charlie Floor-4 VAV_20
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_20 unocc_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_20 unocc_ht_stpt
equip ref: Charlie Floor-4 VAV_20
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_21
type: vav
has tag: equip
has tag: vav
dis: Charlie Floor-4 VAV_21
site ref: Charlie
custom: {equipGroup:VAVs}
  equip group: VAVs

Charlie Floor-4 VAV_21 dpr_pos
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: damper
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_21 dpr_pos
equip ref: Charlie Floor-4 VAV_21
kind: Number
site ref: Charlie
tz: Detroit
unit: %

Charlie Floor-4 VAV_21 eff_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: effective
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_21 eff_cl_stpt
equip ref: Charlie Floor-4 VAV_21
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_21 eff_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: effective
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_21 eff_ht_stpt
equip ref: Charlie Floor-4 VAV_21
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_21 flow_input
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_21 flow_input
equip ref: Charlie Floor-4 VAV_21
kind: Number
max val: 96
min val: 45
site ref: Charlie
tz: Detroit
unit: cfm
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_21 hw_valve
type: cur-point
type: his-point
has tag: cur
has tag: heat
has tag: his
has tag: point
has tag: sensor
has tag: valve
dis: Charlie Floor-4 VAV_21 hw_valve
equip ref: Charlie Floor-4 VAV_21
kind: Number
max val: 100
min val: 0
site ref: Charlie
tz: Detroit
unit: %
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_21 occ_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_21 occ_cl_stpt
equip ref: Charlie Floor-4 VAV_21
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_21 occ_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_21 occ_ht_stpt
equip ref: Charlie Floor-4 VAV_21
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_21 occ_status
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: his
has tag: occupied
has tag: point
dis: Charlie Floor-4 VAV_21 occ_status
enum: Unoccupied,Occupied
equip ref: Charlie Floor-4 VAV_21
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_21 occ_switch
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: occupied
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_21 occ_switch
enum: Open,Closed
equip ref: Charlie Floor-4 VAV_21
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_21 sa_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Charlie Floor-4 VAV_21 sa_temp
equip ref: Charlie Floor-4 VAV_21
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_21 space_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_21 space_temp
equip ref: Charlie Floor-4 VAV_21
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_21 unocc_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_21 unocc_cl_stpt
equip ref: Charlie Floor-4 VAV_21
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_21 unocc_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_21 unocc_ht_stpt
equip ref: Charlie Floor-4 VAV_21
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_22
type: vav
has tag: equip
has tag: vav
dis: Charlie Floor-4 VAV_22
site ref: Charlie
custom: {equipGroup:VAVs}
  equip group: VAVs

Charlie Floor-4 VAV_22 dpr_pos
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: damper
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_22 dpr_pos
equip ref: Charlie Floor-4 VAV_22
kind: Number
site ref: Charlie
tz: Detroit
unit: %

Charlie Floor-4 VAV_22 eff_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: effective
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_22 eff_cl_stpt
equip ref: Charlie Floor-4 VAV_22
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_22 eff_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: effective
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_22 eff_ht_stpt
equip ref: Charlie Floor-4 VAV_22
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_22 flow_input
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_22 flow_input
equip ref: Charlie Floor-4 VAV_22
kind: Number
max val: 96
min val: 45
site ref: Charlie
tz: Detroit
unit: cfm
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_22 hw_valve
type: cur-point
type: his-point
has tag: cur
has tag: heat
has tag: his
has tag: point
has tag: sensor
has tag: valve
dis: Charlie Floor-4 VAV_22 hw_valve
equip ref: Charlie Floor-4 VAV_22
kind: Number
max val: 100
min val: 0
site ref: Charlie
tz: Detroit
unit: %
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_22 occ_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_22 occ_cl_stpt
equip ref: Charlie Floor-4 VAV_22
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_22 occ_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_22 occ_ht_stpt
equip ref: Charlie Floor-4 VAV_22
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_22 occ_status
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: his
has tag: occupied
has tag: point
dis: Charlie Floor-4 VAV_22 occ_status
enum: Unoccupied,Occupied
equip ref: Charlie Floor-4 VAV_22
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_22 occ_switch
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: occupied
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_22 occ_switch
enum: Open,Closed
equip ref: Charlie Floor-4 VAV_22
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_22 sa_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Charlie Floor-4 VAV_22 sa_temp
equip ref: Charlie Floor-4 VAV_22
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_22 space_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_22 space_temp
equip ref: Charlie Floor-4 VAV_22
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_22 unocc_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_22 unocc_cl_stpt
equip ref: Charlie Floor-4 VAV_22
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_22 unocc_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_22 unocc_ht_stpt
equip ref: Charlie Floor-4 VAV_22
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_23
type: vav
has tag: equip
has tag: vav
dis: Charlie Floor-4 VAV_23
site ref: Charlie
custom: {equipGroup:VAVs}
  equip group: VAVs

Charlie Floor-4 VAV_23 dpr_pos
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: damper
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_23 dpr_pos
equip ref: Charlie Floor-4 VAV_23
kind: Number
site ref: Charlie
tz: Detroit
unit: %

Charlie Floor-4 VAV_23 eff_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: effective
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_23 eff_cl_stpt
equip ref: Charlie Floor-4 VAV_23
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_23 eff_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: effective
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_23 eff_ht_stpt
equip ref: Charlie Floor-4 VAV_23
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_23 flow_input
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_23 flow_input
equip ref: Charlie Floor-4 VAV_23
kind: Number
max val: 96
min val: 45
site ref: Charlie
tz: Detroit
unit: cfm
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_23 hw_valve
type: cur-point
type: his-point
has tag: cur
has tag: heat
has tag: his
has tag: point
has tag: sensor
has tag: valve
dis: Charlie Floor-4 VAV_23 hw_valve
equip ref: Charlie Floor-4 VAV_23
kind: Number
max val: 100
min val: 0
site ref: Charlie
tz: Detroit
unit: %
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_23 occ_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_23 occ_cl_stpt
equip ref: Charlie Floor-4 VAV_23
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_23 occ_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_23 occ_ht_stpt
equip ref: Charlie Floor-4 VAV_23
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_23 occ_status
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: his
has tag: occupied
has tag: point
dis: Charlie Floor-4 VAV_23 occ_status
enum: Unoccupied,Occupied
equip ref: Charlie Floor-4 VAV_23
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_23 occ_switch
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: occupied
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_23 occ_switch
enum: Open,Closed
equip ref: Charlie Floor-4 VAV_23
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_23 sa_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Charlie Floor-4 VAV_23 sa_temp
equip ref: Charlie Floor-4 VAV_23
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_23 space_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_23 space_temp
equip ref: Charlie Floor-4 VAV_23
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_23 unocc_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_23 unocc_cl_stpt
equip ref: Charlie Floor-4 VAV_23
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_23 unocc_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_23 unocc_ht_stpt
equip ref: Charlie Floor-4 VAV_23
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_24
type: vav
has tag: equip
has tag: vav
dis: Charlie Floor-4 VAV_24
site ref: Charlie
custom: {equipGroup:VAVs}
  equip group: VAVs

Charlie Floor-4 VAV_24 dpr_pos
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: damper
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_24 dpr_pos
equip ref: Charlie Floor-4 VAV_24
kind: Number
site ref: Charlie
tz: Detroit
unit: %

Charlie Floor-4 VAV_24 eff_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: effective
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_24 eff_cl_stpt
equip ref: Charlie Floor-4 VAV_24
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_24 eff_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: effective
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_24 eff_ht_stpt
equip ref: Charlie Floor-4 VAV_24
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_24 flow_input
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_24 flow_input
equip ref: Charlie Floor-4 VAV_24
kind: Number
max val: 96
min val: 45
site ref: Charlie
tz: Detroit
unit: cfm
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_24 hw_valve
type: cur-point
type: his-point
has tag: cur
has tag: heat
has tag: his
has tag: point
has tag: sensor
has tag: valve
dis: Charlie Floor-4 VAV_24 hw_valve
equip ref: Charlie Floor-4 VAV_24
kind: Number
max val: 100
min val: 0
site ref: Charlie
tz: Detroit
unit: %
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_24 occ_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_24 occ_cl_stpt
equip ref: Charlie Floor-4 VAV_24
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_24 occ_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_24 occ_ht_stpt
equip ref: Charlie Floor-4 VAV_24
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_24 occ_status
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: his
has tag: occupied
has tag: point
dis: Charlie Floor-4 VAV_24 occ_status
enum: Unoccupied,Occupied
equip ref: Charlie Floor-4 VAV_24
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_24 occ_switch
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: occupied
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_24 occ_switch
enum: Open,Closed
equip ref: Charlie Floor-4 VAV_24
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_24 sa_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Charlie Floor-4 VAV_24 sa_temp
equip ref: Charlie Floor-4 VAV_24
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_24 space_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_24 space_temp
equip ref: Charlie Floor-4 VAV_24
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_24 unocc_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_24 unocc_cl_stpt
equip ref: Charlie Floor-4 VAV_24
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_24 unocc_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_24 unocc_ht_stpt
equip ref: Charlie Floor-4 VAV_24
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_25
type: vav
has tag: equip
has tag: vav
dis: Charlie Floor-4 VAV_25
site ref: Charlie
custom: {equipGroup:VAVs}
  equip group: VAVs

Charlie Floor-4 VAV_25 dpr_pos
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: damper
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_25 dpr_pos
equip ref: Charlie Floor-4 VAV_25
kind: Number
site ref: Charlie
tz: Detroit
unit: %

Charlie Floor-4 VAV_25 eff_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: effective
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_25 eff_cl_stpt
equip ref: Charlie Floor-4 VAV_25
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_25 eff_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: effective
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_25 eff_ht_stpt
equip ref: Charlie Floor-4 VAV_25
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_25 flow_input
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_25 flow_input
equip ref: Charlie Floor-4 VAV_25
kind: Number
max val: 96
min val: 45
site ref: Charlie
tz: Detroit
unit: cfm
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_25 hw_valve
type: cur-point
type: his-point
has tag: cur
has tag: heat
has tag: his
has tag: point
has tag: sensor
has tag: valve
dis: Charlie Floor-4 VAV_25 hw_valve
equip ref: Charlie Floor-4 VAV_25
kind: Number
max val: 100
min val: 0
site ref: Charlie
tz: Detroit
unit: %
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_25 link_ahu_mode
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_25 link_ahu_mode
enum: OFF,WARM$2dUP,HEAT,COOL,FREECOOL,PRESSURIZE,EVACUATE,VENT
equip ref: Charlie Floor-4 VAV_25
kind: Str
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_25 occ_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_25 occ_cl_stpt
equip ref: Charlie Floor-4 VAV_25
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_25 occ_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_25 occ_ht_stpt
equip ref: Charlie Floor-4 VAV_25
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_25 occ_status
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: his
has tag: occupied
has tag: point
dis: Charlie Floor-4 VAV_25 occ_status
enum: Unoccupied,Occupied
equip ref: Charlie Floor-4 VAV_25
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_25 occ_switch
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: occupied
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_25 occ_switch
enum: Open,Closed
equip ref: Charlie Floor-4 VAV_25
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_25 sa_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Charlie Floor-4 VAV_25 sa_temp
equip ref: Charlie Floor-4 VAV_25
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_25 space_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_25 space_temp
equip ref: Charlie Floor-4 VAV_25
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_25 terminal_status
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_25 terminal_status
enum: Off,Heating,Warm$2dUp,Vent,N$2fA,Cooling,Dehumidify,Reheat,Pressurize,Evacuate,Shutdown,IAQ$20Override,Air$20Balancing
equip ref: Charlie Floor-4 VAV_25
kind: Str
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_25 unocc_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_25 unocc_cl_stpt
equip ref: Charlie Floor-4 VAV_25
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_25 unocc_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_25 unocc_ht_stpt
equip ref: Charlie Floor-4 VAV_25
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_26
type: vav
has tag: equip
has tag: vav
dis: Charlie Floor-4 VAV_26
site ref: Charlie
custom: {equipGroup:VAVs}
  equip group: VAVs

Charlie Floor-4 VAV_26 dpr_pos
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: damper
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_26 dpr_pos
equip ref: Charlie Floor-4 VAV_26
kind: Number
site ref: Charlie
tz: Detroit
unit: %

Charlie Floor-4 VAV_26 eff_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: effective
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_26 eff_cl_stpt
equip ref: Charlie Floor-4 VAV_26
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_26 eff_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: effective
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_26 eff_ht_stpt
equip ref: Charlie Floor-4 VAV_26
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_26 flow_input
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_26 flow_input
equip ref: Charlie Floor-4 VAV_26
kind: Number
max val: 96
min val: 45
site ref: Charlie
tz: Detroit
unit: cfm
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_26 occ_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_26 occ_cl_stpt
equip ref: Charlie Floor-4 VAV_26
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_26 occ_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_26 occ_ht_stpt
equip ref: Charlie Floor-4 VAV_26
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_26 occ_status
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: his
has tag: occupied
has tag: point
dis: Charlie Floor-4 VAV_26 occ_status
enum: Unoccupied,Occupied
equip ref: Charlie Floor-4 VAV_26
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_26 occ_switch
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: occupied
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_26 occ_switch
enum: Open,Closed
equip ref: Charlie Floor-4 VAV_26
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_26 sa_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Charlie Floor-4 VAV_26 sa_temp
equip ref: Charlie Floor-4 VAV_26
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_26 space_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_26 space_temp
equip ref: Charlie Floor-4 VAV_26
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_26 unocc_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_26 unocc_cl_stpt
equip ref: Charlie Floor-4 VAV_26
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_26 unocc_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_26 unocc_ht_stpt
equip ref: Charlie Floor-4 VAV_26
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_27
type: vav
has tag: equip
has tag: vav
dis: Charlie Floor-4 VAV_27
site ref: Charlie
custom: {equipGroup:VAVs}
  equip group: VAVs

Charlie Floor-4 VAV_27 dpr_pos
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: damper
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_27 dpr_pos
equip ref: Charlie Floor-4 VAV_27
kind: Number
site ref: Charlie
tz: Detroit
unit: %

Charlie Floor-4 VAV_27 eff_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: effective
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_27 eff_cl_stpt
equip ref: Charlie Floor-4 VAV_27
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_27 eff_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: effective
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_27 eff_ht_stpt
equip ref: Charlie Floor-4 VAV_27
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_27 flow_input
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_27 flow_input
equip ref: Charlie Floor-4 VAV_27
kind: Number
max val: 96
min val: 45
site ref: Charlie
tz: Detroit
unit: cfm
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_27 hw_valve
type: cur-point
type: his-point
has tag: cur
has tag: heat
has tag: his
has tag: point
has tag: sensor
has tag: valve
dis: Charlie Floor-4 VAV_27 hw_valve
equip ref: Charlie Floor-4 VAV_27
kind: Number
max val: 100
min val: 0
site ref: Charlie
tz: Detroit
unit: %
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_27 occ_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_27 occ_cl_stpt
equip ref: Charlie Floor-4 VAV_27
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_27 occ_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_27 occ_ht_stpt
equip ref: Charlie Floor-4 VAV_27
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_27 occ_status
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: his
has tag: occupied
has tag: point
dis: Charlie Floor-4 VAV_27 occ_status
enum: Unoccupied,Occupied
equip ref: Charlie Floor-4 VAV_27
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_27 occ_switch
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: occupied
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_27 occ_switch
enum: Open,Closed
equip ref: Charlie Floor-4 VAV_27
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_27 sa_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Charlie Floor-4 VAV_27 sa_temp
equip ref: Charlie Floor-4 VAV_27
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_27 space_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_27 space_temp
equip ref: Charlie Floor-4 VAV_27
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_27 unocc_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_27 unocc_cl_stpt
equip ref: Charlie Floor-4 VAV_27
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_27 unocc_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_27 unocc_ht_stpt
equip ref: Charlie Floor-4 VAV_27
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_28
type: vav
has tag: equip
has tag: vav
dis: Charlie Floor-4 VAV_28
site ref: Charlie
custom: {equipGroup:VAVs}
  equip group: VAVs

Charlie Floor-4 VAV_28 VAVActuatorCommand
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: his
has tag: point
dis: Charlie Floor-4 VAV_28 VAVActuatorCommand
equip ref: Charlie Floor-4 VAV_28
kind: Number
site ref: Charlie
tz: Detroit
unit: %
custom: {precision:1}
  precision: 1

Charlie Floor-4 VAV_28 VAVActuatorPosition
type: cur-point
type: damper-actuator
type: his-point
has tag: actuator
has tag: air
has tag: cur
has tag: damper
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_28 VAVActuatorPosition
equip ref: Charlie Floor-4 VAV_28
kind: Number
site ref: Charlie
tz: Detroit
unit: %
custom: {precision:1, position, actuatorPosition}
  precision: 1

Charlie Floor-4 VAV_28 dpr_pos
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: damper
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_28 dpr_pos
equip ref: Charlie Floor-4 VAV_28
kind: Number
site ref: Charlie
tz: Detroit
unit: %

Charlie Floor-4 VAV_28 eff_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: effective
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_28 eff_cl_stpt
equip ref: Charlie Floor-4 VAV_28
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_28 eff_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: effective
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_28 eff_ht_stpt
equip ref: Charlie Floor-4 VAV_28
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_28 flow_input
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_28 flow_input
equip ref: Charlie Floor-4 VAV_28
kind: Number
max val: 96
min val: 45
site ref: Charlie
tz: Detroit
unit: cfm
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_28 hw_valve
type: cur-point
type: his-point
has tag: cur
has tag: heat
has tag: his
has tag: point
has tag: sensor
has tag: valve
dis: Charlie Floor-4 VAV_28 hw_valve
equip ref: Charlie Floor-4 VAV_28
kind: Number
max val: 100
min val: 0
site ref: Charlie
tz: Detroit
unit: %
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_28 occ_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_28 occ_cl_stpt
equip ref: Charlie Floor-4 VAV_28
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_28 occ_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_28 occ_ht_stpt
equip ref: Charlie Floor-4 VAV_28
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_28 occ_status
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: his
has tag: occupied
has tag: point
dis: Charlie Floor-4 VAV_28 occ_status
enum: Unoccupied,Occupied
equip ref: Charlie Floor-4 VAV_28
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_28 occ_switch
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: occupied
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_28 occ_switch
enum: Open,Closed
equip ref: Charlie Floor-4 VAV_28
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_28 sa_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Charlie Floor-4 VAV_28 sa_temp
equip ref: Charlie Floor-4 VAV_28
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_28 space_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_28 space_temp
equip ref: Charlie Floor-4 VAV_28
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_28 unocc_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_28 unocc_cl_stpt
equip ref: Charlie Floor-4 VAV_28
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_28 unocc_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_28 unocc_ht_stpt
equip ref: Charlie Floor-4 VAV_28
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_29
type: vav
has tag: equip
has tag: vav
dis: Charlie Floor-4 VAV_29
site ref: Charlie
custom: {equipGroup:VAVs}
  equip group: VAVs

Charlie Floor-4 VAV_29 dpr_pos
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: damper
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_29 dpr_pos
equip ref: Charlie Floor-4 VAV_29
kind: Number
site ref: Charlie
tz: Detroit
unit: %

Charlie Floor-4 VAV_29 eff_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: effective
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_29 eff_cl_stpt
equip ref: Charlie Floor-4 VAV_29
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_29 eff_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: effective
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_29 eff_ht_stpt
equip ref: Charlie Floor-4 VAV_29
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_29 flow_input
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_29 flow_input
equip ref: Charlie Floor-4 VAV_29
kind: Number
max val: 96
min val: 45
site ref: Charlie
tz: Detroit
unit: cfm
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_29 hw_valve
type: cur-point
type: his-point
has tag: cur
has tag: heat
has tag: his
has tag: point
has tag: sensor
has tag: valve
dis: Charlie Floor-4 VAV_29 hw_valve
equip ref: Charlie Floor-4 VAV_29
kind: Number
max val: 100
min val: 0
site ref: Charlie
tz: Detroit
unit: %
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_29 occ_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_29 occ_cl_stpt
equip ref: Charlie Floor-4 VAV_29
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_29 occ_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_29 occ_ht_stpt
equip ref: Charlie Floor-4 VAV_29
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_29 occ_status
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: his
has tag: occupied
has tag: point
dis: Charlie Floor-4 VAV_29 occ_status
enum: Unoccupied,Occupied
equip ref: Charlie Floor-4 VAV_29
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_29 occ_switch
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: occupied
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_29 occ_switch
enum: Open,Closed
equip ref: Charlie Floor-4 VAV_29
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_29 sa_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Charlie Floor-4 VAV_29 sa_temp
equip ref: Charlie Floor-4 VAV_29
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_29 space_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_29 space_temp
equip ref: Charlie Floor-4 VAV_29
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_29 unocc_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_29 unocc_cl_stpt
equip ref: Charlie Floor-4 VAV_29
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_29 unocc_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_29 unocc_ht_stpt
equip ref: Charlie Floor-4 VAV_29
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_3
type: vav
has tag: equip
has tag: vav
dis: Charlie Floor-4 VAV_3
site ref: Charlie
custom: {equipGroup:VAVs}
  equip group: VAVs

Charlie Floor-4 VAV_3 dpr_pos
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: damper
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_3 dpr_pos
equip ref: Charlie Floor-4 VAV_3
kind: Number
site ref: Charlie
tz: Detroit
unit: %

Charlie Floor-4 VAV_3 eff_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: effective
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_3 eff_cl_stpt
equip ref: Charlie Floor-4 VAV_3
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_3 eff_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: effective
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_3 eff_ht_stpt
equip ref: Charlie Floor-4 VAV_3
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_3 flow_input
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_3 flow_input
equip ref: Charlie Floor-4 VAV_3
kind: Number
max val: 96
min val: 45
site ref: Charlie
tz: Detroit
unit: cfm
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_3 hw_valve
type: cur-point
type: his-point
has tag: cur
has tag: heat
has tag: his
has tag: point
has tag: sensor
has tag: valve
dis: Charlie Floor-4 VAV_3 hw_valve
equip ref: Charlie Floor-4 VAV_3
kind: Number
max val: 100
min val: 0
site ref: Charlie
tz: Detroit
unit: %
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_3 occ_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_3 occ_cl_stpt
equip ref: Charlie Floor-4 VAV_3
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_3 occ_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_3 occ_ht_stpt
equip ref: Charlie Floor-4 VAV_3
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_3 occ_status
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: his
has tag: occupied
has tag: point
dis: Charlie Floor-4 VAV_3 occ_status
enum: Unoccupied,Occupied
equip ref: Charlie Floor-4 VAV_3
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_3 occ_switch
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: occupied
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_3 occ_switch
enum: Open,Closed
equip ref: Charlie Floor-4 VAV_3
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_3 sa_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Charlie Floor-4 VAV_3 sa_temp
equip ref: Charlie Floor-4 VAV_3
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_3 space_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_3 space_temp
equip ref: Charlie Floor-4 VAV_3
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_3 unocc_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_3 unocc_cl_stpt
equip ref: Charlie Floor-4 VAV_3
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_3 unocc_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_3 unocc_ht_stpt
equip ref: Charlie Floor-4 VAV_3
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_30
type: vav
has tag: equip
has tag: vav
dis: Charlie Floor-4 VAV_30
site ref: Charlie
custom: {equipGroup:VAVs}
  equip group: VAVs

Charlie Floor-4 VAV_30 dpr_pos
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: damper
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_30 dpr_pos
equip ref: Charlie Floor-4 VAV_30
kind: Number
site ref: Charlie
tz: Detroit
unit: %

Charlie Floor-4 VAV_30 eff_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: effective
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_30 eff_cl_stpt
equip ref: Charlie Floor-4 VAV_30
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_30 eff_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: effective
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_30 eff_ht_stpt
equip ref: Charlie Floor-4 VAV_30
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_30 flow_input
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_30 flow_input
equip ref: Charlie Floor-4 VAV_30
kind: Number
max val: 96
min val: 45
site ref: Charlie
tz: Detroit
unit: cfm
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_30 hw_valve
type: cur-point
type: his-point
has tag: cur
has tag: heat
has tag: his
has tag: point
has tag: sensor
has tag: valve
dis: Charlie Floor-4 VAV_30 hw_valve
equip ref: Charlie Floor-4 VAV_30
kind: Number
max val: 100
min val: 0
site ref: Charlie
tz: Detroit
unit: %
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_30 occ_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_30 occ_cl_stpt
equip ref: Charlie Floor-4 VAV_30
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_30 occ_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_30 occ_ht_stpt
equip ref: Charlie Floor-4 VAV_30
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_30 occ_status
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: his
has tag: occupied
has tag: point
dis: Charlie Floor-4 VAV_30 occ_status
enum: Unoccupied,Occupied
equip ref: Charlie Floor-4 VAV_30
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_30 occ_switch
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: occupied
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_30 occ_switch
enum: Open,Closed
equip ref: Charlie Floor-4 VAV_30
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_30 sa_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Charlie Floor-4 VAV_30 sa_temp
equip ref: Charlie Floor-4 VAV_30
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_30 space_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_30 space_temp
equip ref: Charlie Floor-4 VAV_30
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_30 unocc_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_30 unocc_cl_stpt
equip ref: Charlie Floor-4 VAV_30
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_30 unocc_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_30 unocc_ht_stpt
equip ref: Charlie Floor-4 VAV_30
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_4
type: vav
has tag: equip
has tag: vav
dis: Charlie Floor-4 VAV_4
site ref: Charlie
custom: {equipGroup:VAVs}
  equip group: VAVs

Charlie Floor-4 VAV_4 dpr_pos
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: damper
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_4 dpr_pos
equip ref: Charlie Floor-4 VAV_4
kind: Number
site ref: Charlie
tz: Detroit
unit: %

Charlie Floor-4 VAV_4 eff_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: effective
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_4 eff_cl_stpt
equip ref: Charlie Floor-4 VAV_4
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_4 eff_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: effective
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_4 eff_ht_stpt
equip ref: Charlie Floor-4 VAV_4
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_4 flow_input
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_4 flow_input
equip ref: Charlie Floor-4 VAV_4
kind: Number
max val: 96
min val: 45
site ref: Charlie
tz: Detroit
unit: cfm
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_4 hw_valve
type: cur-point
type: his-point
has tag: cur
has tag: heat
has tag: his
has tag: point
has tag: sensor
has tag: valve
dis: Charlie Floor-4 VAV_4 hw_valve
equip ref: Charlie Floor-4 VAV_4
kind: Number
max val: 100
min val: 0
site ref: Charlie
tz: Detroit
unit: %
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_4 occ_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_4 occ_cl_stpt
equip ref: Charlie Floor-4 VAV_4
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_4 occ_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_4 occ_ht_stpt
equip ref: Charlie Floor-4 VAV_4
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_4 occ_status
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: his
has tag: occupied
has tag: point
dis: Charlie Floor-4 VAV_4 occ_status
enum: Unoccupied,Occupied
equip ref: Charlie Floor-4 VAV_4
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_4 occ_switch
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: occupied
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_4 occ_switch
enum: Open,Closed
equip ref: Charlie Floor-4 VAV_4
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_4 sa_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Charlie Floor-4 VAV_4 sa_temp
equip ref: Charlie Floor-4 VAV_4
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_4 space_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_4 space_temp
equip ref: Charlie Floor-4 VAV_4
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_4 unocc_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_4 unocc_cl_stpt
equip ref: Charlie Floor-4 VAV_4
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_4 unocc_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_4 unocc_ht_stpt
equip ref: Charlie Floor-4 VAV_4
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_5
type: vav
has tag: equip
has tag: vav
dis: Charlie Floor-4 VAV_5
site ref: Charlie
custom: {equipGroup:VAVs}
  equip group: VAVs

Charlie Floor-4 VAV_5 dpr_pos
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: damper
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_5 dpr_pos
equip ref: Charlie Floor-4 VAV_5
kind: Number
site ref: Charlie
tz: Detroit
unit: %

Charlie Floor-4 VAV_5 eff_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: effective
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_5 eff_cl_stpt
equip ref: Charlie Floor-4 VAV_5
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_5 eff_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: effective
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_5 eff_ht_stpt
equip ref: Charlie Floor-4 VAV_5
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_5 flow_input
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_5 flow_input
equip ref: Charlie Floor-4 VAV_5
kind: Number
max val: 96
min val: 45
site ref: Charlie
tz: Detroit
unit: cfm
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_5 hw_valve
type: cur-point
type: his-point
has tag: cur
has tag: heat
has tag: his
has tag: point
has tag: sensor
has tag: valve
dis: Charlie Floor-4 VAV_5 hw_valve
equip ref: Charlie Floor-4 VAV_5
kind: Number
max val: 100
min val: 0
site ref: Charlie
tz: Detroit
unit: %
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_5 occ_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_5 occ_cl_stpt
equip ref: Charlie Floor-4 VAV_5
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_5 occ_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_5 occ_ht_stpt
equip ref: Charlie Floor-4 VAV_5
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_5 occ_status
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: his
has tag: occupied
has tag: point
dis: Charlie Floor-4 VAV_5 occ_status
enum: Unoccupied,Occupied
equip ref: Charlie Floor-4 VAV_5
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_5 occ_switch
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: occupied
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_5 occ_switch
enum: Open,Closed
equip ref: Charlie Floor-4 VAV_5
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_5 sa_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Charlie Floor-4 VAV_5 sa_temp
equip ref: Charlie Floor-4 VAV_5
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_5 space_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_5 space_temp
equip ref: Charlie Floor-4 VAV_5
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_5 unocc_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_5 unocc_cl_stpt
equip ref: Charlie Floor-4 VAV_5
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_5 unocc_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_5 unocc_ht_stpt
equip ref: Charlie Floor-4 VAV_5
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_6
type: vav
has tag: equip
has tag: vav
dis: Charlie Floor-4 VAV_6
site ref: Charlie
custom: {equipGroup:VAVs}
  equip group: VAVs

Charlie Floor-4 VAV_6 dpr_pos
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: damper
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_6 dpr_pos
equip ref: Charlie Floor-4 VAV_6
kind: Number
site ref: Charlie
tz: Detroit
unit: %

Charlie Floor-4 VAV_6 eff_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: effective
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_6 eff_cl_stpt
equip ref: Charlie Floor-4 VAV_6
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_6 eff_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: effective
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_6 eff_ht_stpt
equip ref: Charlie Floor-4 VAV_6
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_6 flow_input
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_6 flow_input
equip ref: Charlie Floor-4 VAV_6
kind: Number
max val: 96
min val: 45
site ref: Charlie
tz: Detroit
unit: cfm
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_6 hw_valve
type: cur-point
type: his-point
has tag: cur
has tag: heat
has tag: his
has tag: point
has tag: sensor
has tag: valve
dis: Charlie Floor-4 VAV_6 hw_valve
equip ref: Charlie Floor-4 VAV_6
kind: Number
max val: 100
min val: 0
site ref: Charlie
tz: Detroit
unit: %
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_6 occ_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_6 occ_cl_stpt
equip ref: Charlie Floor-4 VAV_6
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_6 occ_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_6 occ_ht_stpt
equip ref: Charlie Floor-4 VAV_6
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_6 occ_status
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: his
has tag: occupied
has tag: point
dis: Charlie Floor-4 VAV_6 occ_status
enum: Unoccupied,Occupied
equip ref: Charlie Floor-4 VAV_6
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_6 occ_switch
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: occupied
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_6 occ_switch
enum: Open,Closed
equip ref: Charlie Floor-4 VAV_6
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_6 sa_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Charlie Floor-4 VAV_6 sa_temp
equip ref: Charlie Floor-4 VAV_6
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_6 space_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_6 space_temp
equip ref: Charlie Floor-4 VAV_6
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_6 unocc_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_6 unocc_cl_stpt
equip ref: Charlie Floor-4 VAV_6
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_6 unocc_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_6 unocc_ht_stpt
equip ref: Charlie Floor-4 VAV_6
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_7
type: vav
has tag: equip
has tag: vav
dis: Charlie Floor-4 VAV_7
site ref: Charlie
custom: {equipGroup:VAVs}
  equip group: VAVs

Charlie Floor-4 VAV_7 dpr_pos
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: damper
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_7 dpr_pos
equip ref: Charlie Floor-4 VAV_7
kind: Number
site ref: Charlie
tz: Detroit
unit: %

Charlie Floor-4 VAV_7 eff_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: effective
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_7 eff_cl_stpt
equip ref: Charlie Floor-4 VAV_7
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_7 eff_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: effective
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_7 eff_ht_stpt
equip ref: Charlie Floor-4 VAV_7
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_7 flow_input
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_7 flow_input
equip ref: Charlie Floor-4 VAV_7
kind: Number
max val: 96
min val: 45
site ref: Charlie
tz: Detroit
unit: cfm
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_7 hw_valve
type: cur-point
type: his-point
has tag: cur
has tag: heat
has tag: his
has tag: point
has tag: sensor
has tag: valve
dis: Charlie Floor-4 VAV_7 hw_valve
equip ref: Charlie Floor-4 VAV_7
kind: Number
max val: 100
min val: 0
site ref: Charlie
tz: Detroit
unit: %
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_7 occ_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_7 occ_cl_stpt
equip ref: Charlie Floor-4 VAV_7
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_7 occ_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_7 occ_ht_stpt
equip ref: Charlie Floor-4 VAV_7
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_7 occ_status
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: his
has tag: occupied
has tag: point
dis: Charlie Floor-4 VAV_7 occ_status
enum: Unoccupied,Occupied
equip ref: Charlie Floor-4 VAV_7
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_7 occ_switch
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: occupied
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_7 occ_switch
enum: Open,Closed
equip ref: Charlie Floor-4 VAV_7
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_7 sa_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Charlie Floor-4 VAV_7 sa_temp
equip ref: Charlie Floor-4 VAV_7
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_7 space_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_7 space_temp
equip ref: Charlie Floor-4 VAV_7
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_7 unocc_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_7 unocc_cl_stpt
equip ref: Charlie Floor-4 VAV_7
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_7 unocc_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_7 unocc_ht_stpt
equip ref: Charlie Floor-4 VAV_7
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_8
type: vav
has tag: equip
has tag: vav
dis: Charlie Floor-4 VAV_8
site ref: Charlie
custom: {equipGroup:VAVs}
  equip group: VAVs

Charlie Floor-4 VAV_8 dpr_pos
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: damper
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_8 dpr_pos
equip ref: Charlie Floor-4 VAV_8
kind: Number
site ref: Charlie
tz: Detroit
unit: %

Charlie Floor-4 VAV_8 eff_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: effective
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_8 eff_cl_stpt
equip ref: Charlie Floor-4 VAV_8
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_8 eff_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: effective
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_8 eff_ht_stpt
equip ref: Charlie Floor-4 VAV_8
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_8 flow_input
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_8 flow_input
equip ref: Charlie Floor-4 VAV_8
kind: Number
max val: 96
min val: 45
site ref: Charlie
tz: Detroit
unit: cfm
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_8 hw_valve
type: cur-point
type: his-point
has tag: cur
has tag: heat
has tag: his
has tag: point
has tag: sensor
has tag: valve
dis: Charlie Floor-4 VAV_8 hw_valve
equip ref: Charlie Floor-4 VAV_8
kind: Number
max val: 100
min val: 0
site ref: Charlie
tz: Detroit
unit: %
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_8 occ_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_8 occ_cl_stpt
equip ref: Charlie Floor-4 VAV_8
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_8 occ_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_8 occ_ht_stpt
equip ref: Charlie Floor-4 VAV_8
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_8 occ_status
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: his
has tag: occupied
has tag: point
dis: Charlie Floor-4 VAV_8 occ_status
enum: Unoccupied,Occupied
equip ref: Charlie Floor-4 VAV_8
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_8 occ_switch
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: occupied
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_8 occ_switch
enum: Open,Closed
equip ref: Charlie Floor-4 VAV_8
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_8 sa_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Charlie Floor-4 VAV_8 sa_temp
equip ref: Charlie Floor-4 VAV_8
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_8 space_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_8 space_temp
equip ref: Charlie Floor-4 VAV_8
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_8 unocc_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_8 unocc_cl_stpt
equip ref: Charlie Floor-4 VAV_8
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_8 unocc_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_8 unocc_ht_stpt
equip ref: Charlie Floor-4 VAV_8
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_9
type: vav
has tag: equip
has tag: vav
dis: Charlie Floor-4 VAV_9
site ref: Charlie
custom: {equipGroup:VAVs}
  equip group: VAVs

Charlie Floor-4 VAV_9 dpr_pos
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: damper
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_9 dpr_pos
equip ref: Charlie Floor-4 VAV_9
kind: Number
site ref: Charlie
tz: Detroit
unit: %

Charlie Floor-4 VAV_9 eff_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: effective
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_9 eff_cl_stpt
equip ref: Charlie Floor-4 VAV_9
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_9 eff_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: effective
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_9 eff_ht_stpt
equip ref: Charlie Floor-4 VAV_9
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_9 flow_input
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: flow
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_9 flow_input
equip ref: Charlie Floor-4 VAV_9
kind: Number
max val: 96
min val: 45
site ref: Charlie
tz: Detroit
unit: cfm
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_9 hw_valve
type: cur-point
type: his-point
has tag: cur
has tag: heat
has tag: his
has tag: point
has tag: sensor
has tag: valve
dis: Charlie Floor-4 VAV_9 hw_valve
equip ref: Charlie Floor-4 VAV_9
kind: Number
max val: 100
min val: 0
site ref: Charlie
tz: Detroit
unit: %
custom: {precision:0}
  precision: 0

Charlie Floor-4 VAV_9 link_ahu_mode
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_9 link_ahu_mode
enum: OFF,WARM$2dUP,HEAT,COOL,FREECOOL,PRESSURIZE,EVACUATE,VENT
equip ref: Charlie Floor-4 VAV_9
kind: Str
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_9 occ_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_9 occ_cl_stpt
equip ref: Charlie Floor-4 VAV_9
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_9 occ_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: occ
has tag: point
has tag: sp
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_9 occ_ht_stpt
equip ref: Charlie Floor-4 VAV_9
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_9 occ_status
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: his
has tag: occupied
has tag: point
dis: Charlie Floor-4 VAV_9 occ_status
enum: Unoccupied,Occupied
equip ref: Charlie Floor-4 VAV_9
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_9 occ_switch
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: occupied
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_9 occ_switch
enum: Open,Closed
equip ref: Charlie Floor-4 VAV_9
kind: Bool
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_9 sa_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Charlie Floor-4 VAV_9 sa_temp
equip ref: Charlie Floor-4 VAV_9
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_9 space_temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Charlie Floor-4 VAV_9 space_temp
equip ref: Charlie Floor-4 VAV_9
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_9 terminal_status
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: point
has tag: sensor
dis: Charlie Floor-4 VAV_9 terminal_status
enum: Off,Heating,Warm$2dUp,Vent,N$2fA,Cooling,Dehumidify,Reheat,Pressurize,Evacuate,Shutdown,IAQ$20Override,Air$20Balancing
equip ref: Charlie Floor-4 VAV_9
kind: Str
site ref: Charlie
tz: Detroit

Charlie Floor-4 VAV_9 unocc_cl_stpt
type: cur-point
type: his-point
has tag: air
has tag: cooling
has tag: cur
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_9 unocc_cl_stpt
equip ref: Charlie Floor-4 VAV_9
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie Floor-4 VAV_9 unocc_ht_stpt
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: heating
has tag: his
has tag: point
has tag: sp
has tag: temp
has tag: unocc
has tag: zone
dis: Charlie Floor-4 VAV_9 unocc_ht_stpt
equip ref: Charlie Floor-4 VAV_9
kind: Number
site ref: Charlie
tz: Detroit
unit: °F

Charlie HEATING UNIT-1
type: ahu
has tag: ahu
has tag: equip
dis: Charlie HEATING UNIT-1
site ref: Charlie
custom: {unitHeater, equipGroup:AHUs}
  equip group: AHUs

Charlie HEATING UNIT-1 Discharge Air Temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Charlie HEATING UNIT-1 Discharge Air Temp
equip ref: Charlie HEATING UNIT-1
kind: Number
site ref: Charlie
tz: New_York
unit: °F

Charlie HEATING UNIT-1 HeatUnit-SF~2dS
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: fan
has tag: his
has tag: point
has tag: sensor
dis: Charlie HEATING UNIT-1 HeatUnit-SF~2dS
enum: Off,On
equip ref: Charlie HEATING UNIT-1
kind: Bool
site ref: Charlie
tz: New_York

Charlie HEATING UNIT-1 HeatUnit1-DA~2dP--
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: pressure
has tag: sensor
dis: Charlie HEATING UNIT-1 HeatUnit1-DA~2dP--
equip ref: Charlie HEATING UNIT-1
kind: Number
site ref: Charlie
tz: New_York
unit: in/wc
custom: {precision:2}
  precision: 2

Charlie HEATING UNIT-1 HeatUnit1-DA~2dP-SetPoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: pressure
has tag: sp
dis: Charlie HEATING UNIT-1 HeatUnit1-DA~2dP-SetPoint
equip ref: Charlie HEATING UNIT-1
kind: Number
site ref: Charlie
tz: New_York
unit: in/wc
custom: {precision:2}
  precision: 2

Charlie HEATING UNIT-1 HeatUnit1-Discharge Air Temp-Reset
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sp
has tag: temp
dis: Charlie HEATING UNIT-1 HeatUnit1-Discharge Air Temp-Reset
equip ref: Charlie HEATING UNIT-1
kind: Number
site ref: Charlie
tz: New_York
unit: °F
custom: {reset}

Charlie HEATING UNIT-1 HeatUnit1-HW~2dValve
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Charlie HEATING UNIT-1 HeatUnit1-HW~2dValve
equip ref: Charlie HEATING UNIT-1
kind: Number
site ref: Charlie
tz: New_York
unit: %

Charlie HEATING UNIT-1 HeatUnit1-OCC~2dC
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: his
has tag: occupied
has tag: point
dis: Charlie HEATING UNIT-1 HeatUnit1-OCC~2dC
enum: UnOccupied,Occupied
equip ref: Charlie HEATING UNIT-1
kind: Bool
site ref: Charlie
tz: New_York

Charlie HEATING UNIT-1 HeatUnit1-SF~2dC
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: discharge
has tag: fan
has tag: his
has tag: point
dis: Charlie HEATING UNIT-1 HeatUnit1-SF~2dC
enum: Off,On
equip ref: Charlie HEATING UNIT-1
kind: Bool
site ref: Charlie
tz: New_York

Charlie HEATING UNIT-1 HeatUnit1-SF~2dVFD
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: discharge
has tag: fan
has tag: his
has tag: point
has tag: speed
dis: Charlie HEATING UNIT-1 HeatUnit1-SF~2dVFD
equip ref: Charlie HEATING UNIT-1
kind: Number
site ref: Charlie
tz: New_York
unit: %

Charlie HEATING UNIT-1 SupplyFan
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: discharge
has tag: fan
has tag: his
has tag: point
dis: Charlie HEATING UNIT-1 SupplyFan
enum: false,true
equip ref: Charlie HEATING UNIT-1
kind: Bool
site ref: Charlie
tz: New_York

Charlie HEATING UNIT-1 SupplyfanStatus
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: fan
has tag: his
has tag: point
has tag: run
has tag: sensor
dis: Charlie HEATING UNIT-1 SupplyfanStatus
enum: false,true
equip ref: Charlie HEATING UNIT-1
kind: Bool
site ref: Charlie
tz: New_York

Charlie HEATING UNIT-1 Zone Air Temp Sensor
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Charlie HEATING UNIT-1 Zone Air Temp Sensor
equip ref: Charlie HEATING UNIT-1
kind: Number
site ref: Charlie
tz: New_York
unit: °F

Charlie HEATING UNIT-2
type: ahu
has tag: ahu
has tag: equip
dis: Charlie HEATING UNIT-2
site ref: Charlie
custom: {unitHeater, equipGroup:AHUs}
  equip group: AHUs

Charlie HEATING UNIT-2 Discharge Air Temp
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: sensor
has tag: temp
dis: Charlie HEATING UNIT-2 Discharge Air Temp
equip ref: Charlie HEATING UNIT-2
kind: Number
site ref: Charlie
tz: New_York
unit: °F

Charlie HEATING UNIT-2 HeatUnit2-DA~2dP
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: pressure
has tag: sensor
dis: Charlie HEATING UNIT-2 HeatUnit2-DA~2dP
equip ref: Charlie HEATING UNIT-2
kind: Number
site ref: Charlie
tz: New_York
unit: in/wc
custom: {precision:2}
  precision: 2

Charlie HEATING UNIT-2 HeatUnit2-DA~2dP-SetPoint
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: his
has tag: point
has tag: pressure
has tag: sp
dis: Charlie HEATING UNIT-2 HeatUnit2-DA~2dP-SetPoint
equip ref: Charlie HEATING UNIT-2
kind: Number
site ref: Charlie
tz: New_York
unit: in/wc
custom: {precision:2}
  precision: 2

Charlie HEATING UNIT-2 HeatUnit2-HW~2dValve
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: his
has tag: hot
has tag: point
has tag: valve
has tag: water
dis: Charlie HEATING UNIT-2 HeatUnit2-HW~2dValve
equip ref: Charlie HEATING UNIT-2
kind: Number
site ref: Charlie
tz: New_York
unit: %

Charlie HEATING UNIT-2 HeatUnit2-OCC~2dC
type: cur-point
type: his-point
has tag: cmd
has tag: cur
has tag: his
has tag: occupied
has tag: point
dis: Charlie HEATING UNIT-2 HeatUnit2-OCC~2dC
enum: UnOccupied,Occupied
equip ref: Charlie HEATING UNIT-2
kind: Bool
site ref: Charlie
tz: New_York

Charlie HEATING UNIT-2 HeatUnit2-SF~2dC
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: discharge
has tag: fan
has tag: his
has tag: point
dis: Charlie HEATING UNIT-2 HeatUnit2-SF~2dC
enum: Off,On
equip ref: Charlie HEATING UNIT-2
kind: Bool
site ref: Charlie
tz: New_York

Charlie HEATING UNIT-2 HeatUnit2-SF~2dS
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: fan
has tag: his
has tag: point
has tag: sensor
dis: Charlie HEATING UNIT-2 HeatUnit2-SF~2dS
enum: Off,On
equip ref: Charlie HEATING UNIT-2
kind: Bool
site ref: Charlie
tz: New_York

Charlie HEATING UNIT-2 HeatUnit2-SF~2dVFD
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: discharge
has tag: fan
has tag: his
has tag: point
has tag: speed
dis: Charlie HEATING UNIT-2 HeatUnit2-SF~2dVFD
equip ref: Charlie HEATING UNIT-2
kind: Number
site ref: Charlie
tz: New_York
unit: %

Charlie HEATING UNIT-2 SupplyFan
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: discharge
has tag: fan
has tag: his
has tag: point
dis: Charlie HEATING UNIT-2 SupplyFan
enum: false,true
equip ref: Charlie HEATING UNIT-2
kind: Bool
site ref: Charlie
tz: New_York

Charlie HEATING UNIT-2 SupplyfanStatus
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: discharge
has tag: fan
has tag: his
has tag: point
has tag: run
has tag: sensor
dis: Charlie HEATING UNIT-2 SupplyfanStatus
enum: false,true
equip ref: Charlie HEATING UNIT-2
kind: Bool
site ref: Charlie
tz: New_York

Charlie HEATING UNIT-2 Zone Air Temp Sensor
type: cur-point
type: his-point
has tag: air
has tag: cur
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: zone
dis: Charlie HEATING UNIT-2 Zone Air Temp Sensor
equip ref: Charlie HEATING UNIT-2
kind: Number
site ref: Charlie
tz: New_York
unit: °F

Charlie LIBERTY_100_LIGHTING
type: equip
has tag: equip
dis: Charlie LIBERTY_100_LIGHTING
site ref: Charlie
custom: {lightsGroup, equipGroup:Lighting System}
  equip group: Lighting System

Charlie LIBERTY_100_LIGHTING Photo-Cell
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: light
has tag: point
has tag: sensor
dis: Charlie LIBERTY_100_LIGHTING Photo-Cell
equip ref: Charlie LIBERTY_100_LIGHTING
kind: Number
site ref: Charlie
tz: New_York
unit: lx
custom: {precision:1}
  precision: 1

Charlie LIBERTY_100_LIGHTING VAVActuatorCommand
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: his
has tag: point
dis: Charlie LIBERTY_100_LIGHTING VAVActuatorCommand
equip ref: Charlie LIBERTY_100_LIGHTING
kind: Number
site ref: Charlie
tz: Detroit
unit: %
custom: {precision:1}
  precision: 1

Charlie LIBERTY_100_LIGHTING VAVActuatorCommand
type: cur-point
type: his-point
has tag: air
has tag: cmd
has tag: cur
has tag: damper
has tag: his
has tag: point
dis: Charlie LIBERTY_100_LIGHTING VAVActuatorCommand
equip ref: Charlie LIBERTY_100_LIGHTING
kind: Number
site ref: Charlie
tz: Detroit
unit: %
custom: {precision:1}
  precision: 1

Charlie LIBERTY_100_LIGHTING VAVActuatorPosition
type: cur-point
type: damper-actuator
type: his-point
has tag: actuator
has tag: air
has tag: cur
has tag: damper
has tag: his
has tag: point
has tag: sensor
dis: Charlie LIBERTY_100_LIGHTING VAVActuatorPosition
equip ref: Charlie LIBERTY_100_LIGHTING
kind: Number
site ref: Charlie
tz: Detroit
unit: %
custom: {precision:1, position, actuatorPosition}
  precision: 1

Charlie LIBERTY_100_LIGHTING VAVActuatorPosition
type: cur-point
type: damper-actuator
type: his-point
has tag: actuator
has tag: air
has tag: cur
has tag: damper
has tag: his
has tag: point
has tag: sensor
dis: Charlie LIBERTY_100_LIGHTING VAVActuatorPosition
equip ref: Charlie LIBERTY_100_LIGHTING
kind: Number
site ref: Charlie
tz: Detroit
unit: %
custom: {precision:1, position, actuatorPosition}
  precision: 1

Charlie Water_Main_100_Meter
type: ac-elec-meter
has tag: ac
has tag: elec
has tag: equip
has tag: meter
has tag: water
dis: Charlie Water_Main_100_Meter
site ref: Charlie
custom: {equipGroup:Meters}
  equip group: Meters

Charlie Water_Main_100_Meter chA mass flow
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: point
has tag: sensor
dis: Charlie Water_Main_100_Meter chA mass flow
equip ref: Charlie Water_Main_100_Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: lb/h

Charlie Water_Main_100_Meter chA volumetric flow rate
type: cur-point
type: his-point
has tag: cur
has tag: flow
has tag: his
has tag: point
has tag: sensor
has tag: volume
has tag: water
dis: Charlie Water_Main_100_Meter chA volumetric flow rate
equip ref: Charlie Water_Main_100_Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: gal/min
custom: {pointType:}

Charlie Water_Main_100_Meter chA volumetric flow rate, + totalizer
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: point
has tag: sensor
dis: Charlie Water_Main_100_Meter chA volumetric flow rate, + totalizer
equip ref: Charlie Water_Main_100_Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: gal

Charlie West_Return_Fan_Meter
type: ac-elec-meter
has tag: ac
has tag: elec
has tag: equip
has tag: meter
dis: Charlie West_Return_Fan_Meter
equip ref: Charlie AHU-2
site ref: Charlie
submeter of: Charlie Elec_Main_100_Meter
custom: {equipGroup:Meters}
  equip group: Meters

Charlie West_Return_Fan_Meter Current Sum Element G
type: cur-point
type: his-point
has tag: cur
has tag: current
has tag: his
has tag: point
has tag: sensor
dis: Charlie West_Return_Fan_Meter Current Sum Element G
equip ref: Charlie West_Return_Fan_Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: A

Charlie West_Return_Fan_Meter Fan VA Sum Element G
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: point
has tag: reactive
has tag: sensor
dis: Charlie West_Return_Fan_Meter Fan VA Sum Element G
equip ref: Charlie West_Return_Fan_Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: kVA

Charlie West_Return_Fan_Meter Power Demand Peak Element G
type: cur-point
type: his-point
has tag: ac
has tag: cur
has tag: demand
has tag: elec
has tag: his
has tag: point
has tag: power
has tag: sensor
dis: Charlie West_Return_Fan_Meter Power Demand Peak Element G
equip ref: Charlie West_Return_Fan_Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: kW

Charlie West_Return_Fan_Meter Power Sum Element G
type: cur-point
type: his-point
has tag: ac
has tag: cur
has tag: elec
has tag: his
has tag: point
has tag: power
has tag: sensor
dis: Charlie West_Return_Fan_Meter Power Sum Element G
equip ref: Charlie West_Return_Fan_Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: kW

Charlie West_Return_Fan_Meter VA Demand Peak Element G
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: point
has tag: reactive
has tag: sensor
dis: Charlie West_Return_Fan_Meter VA Demand Peak Element G
equip ref: Charlie West_Return_Fan_Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: kVA

Charlie West_Supply_Fan_Meter
type: ac-elec-meter
has tag: ac
has tag: elec
has tag: equip
has tag: his
has tag: meter
dis: Charlie West_Supply_Fan_Meter
equip ref: Charlie AHU-2
site ref: Charlie
submeter of: Charlie Elec_Main_100_Meter
custom: {equipGroup:Meters}
  equip group: Meters

Charlie West_Supply_Fan_Meter Current Sum Element P
type: cur-point
type: his-point
has tag: cur
has tag: current
has tag: his
has tag: point
has tag: sensor
dis: Charlie West_Supply_Fan_Meter Current Sum Element P
equip ref: Charlie West_Supply_Fan_Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: A

Charlie West_Supply_Fan_Meter Power Demand Peak Element P
type: cur-point
type: his-point
has tag: ac
has tag: cur
has tag: demand
has tag: elec
has tag: his
has tag: point
has tag: power
has tag: sensor
dis: Charlie West_Supply_Fan_Meter Power Demand Peak Element P
equip ref: Charlie West_Supply_Fan_Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: kW

Charlie West_Supply_Fan_Meter Power Sum Element P
type: cur-point
type: his-point
has tag: ac
has tag: cur
has tag: elec
has tag: his
has tag: point
has tag: power
has tag: sensor
dis: Charlie West_Supply_Fan_Meter Power Sum Element P
equip ref: Charlie West_Supply_Fan_Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: kW

Charlie West_Supply_Fan_Meter VA Demand Peak Element P
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: point
has tag: reactive
has tag: sensor
dis: Charlie West_Supply_Fan_Meter VA Demand Peak Element P
equip ref: Charlie West_Supply_Fan_Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: kVA

Charlie West_Supply_Fan_Meter VA Sum Element P
type: cur-point
type: his-point
has tag: cur
has tag: his
has tag: point
has tag: reactive
has tag: sensor
dis: Charlie West_Supply_Fan_Meter VA Sum Element P
equip ref: Charlie West_Supply_Fan_Meter
kind: Number
site ref: Charlie
tz: Detroit
unit: kVA

Troy, MI
type: weatherStation
has tag: weatherStation
dis: Troy, MI
geo city: Troy
geo coord: C(42.606,-83.15)
geo country: US
geo state: MI
tz: Detroit

Troy, MI Barometric Pressure
type: his-point
type: weather-point
has tag: atmospheric
has tag: his
has tag: point
has tag: pressure
has tag: sensor
has tag: weather
dis: Troy, MI Barometric Pressure
kind: Number
tz: Detroit
unit: inHg
weather station ref: Troy, MI

Troy, MI Condition
type: his-point
type: weather-point
has tag: his
has tag: point
has tag: sensor
has tag: weather
has tag: weatherCond
dis: Troy, MI Condition
enum: unknown,clear,partlyCloudy,cloudy,showers,rain,thunderstorms,ice,flurries,snow
kind: Str
tz: Detroit
weather station ref: Troy, MI

Troy, MI Dew Point
type: his-point
type: weather-point
has tag: dewPoint
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: weather
dis: Troy, MI Dew Point
kind: Number
tz: Detroit
unit: °F
weather station ref: Troy, MI

Troy, MI Feels Like
type: his-point
type: weather-point
has tag: feelsLike
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: weather
dis: Troy, MI Feels Like
kind: Number
tz: Detroit
unit: °F
weather station ref: Troy, MI

Troy, MI Humidity
type: his-point
type: weather-point
has tag: air
has tag: his
has tag: humidity
has tag: point
has tag: sensor
has tag: weather
dis: Troy, MI Humidity
kind: Number
tz: Detroit
unit: %RH
weather station ref: Troy, MI

Troy, MI Precipitation
type: his-point
type: weather-point
has tag: his
has tag: point
has tag: precipitation
has tag: sensor
has tag: weather
dis: Troy, MI Precipitation
kind: Number
tz: Detroit
unit: in
weather station ref: Troy, MI

Troy, MI Sunrise
type: his-point
type: weather-point
has tag: daytime
has tag: his
has tag: point
has tag: sensor
has tag: weather
dis: Troy, MI Sunrise
kind: Bool
tz: Detroit
weather station ref: Troy, MI

Troy, MI Temp
type: his-point
type: weather-point
has tag: air
has tag: his
has tag: point
has tag: sensor
has tag: temp
has tag: weather
dis: Troy, MI Temp
kind: Number
tz: Detroit
unit: °F
weather station ref: Troy, MI