Equip level of the lighting system which is a group of one or more
Lighting Groups (Equip)
Lighting groups may model a single light switch, room, physical circuit, lighting panel, or logical grouping of lights. The lighting group purpose is primarily to organize one or more lighting points to match the standardized site+equip+point model for navigation and analytics.
The following are the standard point types under lighting group:
lights: primary actuator point indicating whether the lights are commanded on/off. The lights point must be either a binary point (on/off) or a numeric point if dimmable (0% to 100%). A lightsGroup must have one or more of these points.
lightLevel: sensor indicating current lighting level measured in "lux" or "lumen". A lightsGroup can have zero or more of these points.
occupancyIndicator: sensor indicating whether room is currently occupied. Point must be Bool where true indicates occupied and false indicates unoccupied. A lightsGroup can have zero or more of these points.